- Power transformers are used in transmission network of higher voltages for step-up and step down application (400 kV, 200 kV, 110 kV, 66 kV, 33kV) and are generally rated above 200MVA.
- Distribution transformers are used for lower voltage distribution networks as a means to end user connectivity. (11kV, 6.6 kV, 3.3 kV, 440V, 230V) and are generally rated less than 200 MVA.
- A power transformer usually has one primary and one secondary, and one input and output. A distribution transformer may have one primary and one divided or “Tapped” secondary, or two or more secondaries.
- Power transformers generally operate at nearly full – load. However, a distribution transformer operates at light loads during major parts of the day.
- The performance of the power transformers is generally judged from commercial efficiency whereas the performance of a distribution transformer is judged from all – day – efficiency.
- The rating of a high transformer is many times greater than that of distribution transformer.
- In Power Transformer the flux density is higher than the distribution transformer.
- Power transformer’s primary winding always connected in star and secondary winding in delta while in distribution transformer primary winding connected in delta and secondary in star.
- In The Sub station end of the transmission line, The Power Transformer Connection is Star-Delta.( For the purpose of Step down the Voltage Level)
- In the star up of the Transmission line (H-T), The Connection of the power Transformer is Delta – Star (For the purpose of Step Up the Voltage Level) But in case of Distribution Transformer, But Generally it is used in there-phase Step down distribution transformer( Delta – Star).
(Click To enlarge the image)
Register now to use it for free in Your Browser. No Need to download. Lots of resources and Step by step tutorials