Why Motor rated in kW instead of kVA
Why Motor rated in kW/Horsepower instead of kVA?
We know that Transformer rating may be expressed in kVA as well as Generator and Alternator rated in kVA Designer doesn’t know the actual consumer power factor while manufacturing transformers and generators i.e. the P.F (Power factor) of Transformer and Generator/Alternator depends on the nature of connected load such as resistive load, capacitive load, and inductive load as Motors, etc. But Motorhas fixed Power factor, i.e. motor has defined power factor and the rating has been mentioned in KW on Motor nameplate data table. That’s why we are rated Motor in kW or HP (kilowatts/ Horsepower) instead of kVA.
Why Power Plant Capacity Rated in MW and not in MVA?
Free Circuit Design Software: learn to use Editor quickly and easily
Cheapest PCB: 10pcs 2-layers 10cm×10cm only $8.21, 3-day build time, 100% E-test