Cable Size Calculator in AWG
As we have already discussed that how to select the proper wire size for Electrical wiring installationin detail under the topic of How to determine the suitable size ofcable for Electrical Wiring Installation with Solved Examples (in both British and Si System). Now we are here to present the Wire and cable size calculator for you.
 You have also check the Wire & Cable Size Calculator (Cupper & Aluminum) in AWG (American Wire Gauge)
Calculating Wire/Cable Size formula for single Phase Circuits
Wire Circular mils =2 x ρ x I x L / (%Allowable Voltage drop of source voltage)
Calculating Wire/Cable Size formula for Three Phase Circuits
Wire Circular mils =√3 x 2 x ρ x I x L / (%Allowable Voltage drop of source voltage)
Where;
ρ = Specific resistance or resistivity of Conductor
D = Distance in Feet (One way) i.e. ½ the total circuit length
I = Load Current
Note: the Value of ρ = Specific resistance or resistivity of Conductor is used here for copper and aluminum is 12.9 and 21.2 respectively at 75°C (167°F).
 Also check the “Good to know” Section after the calculator
Enter value, And click on calculate. Result will show the required quantity.
Good to Know:
If the wire size is greater than all gauges (i.e 0000 is largest one size of wire in), then electrical engineer measure it in CM, kCM or MCM instead of inches, because inch is a small unit of these kinds of wires. Where;
A circular mil (CM) is a unit of circular area with a diameter of one mil (one thousandth of an inch). It corresponds to 5.067×10^{4} mm².
Where:
1000 CM (circular mils) = 1 MCM or 1 kcmil = 0.5067 mm², so 2 kcmil.
It is a unit for referring to the area of a wire with a circular cross section.

Also Check: Advance Voltage Drop Calculator
China's Largest PCB Prototype Manufacturer, with 290,000+ Customers & 8,000+ Orders Per Day
10 PCBs Price: $2 for 2layer, $15 for 4layer, $74 for 6layer
Hi thanks for the wonderful information. How can I download that calculator? I am very glad if if you will help me thank you very much
Dear Carlo!
Thanks for appreciation.. We are working on it. and it will be available for both Android and iOS stores… (Very Soon). once again Thanks.
i want to enter value of voltage level !!! as well as current value also !!!
Yes! you can. just check it Here.
Hey I want a formula through which i can find relation between Conductor size and current carrying capacity of it????
Dear Sir,
Can you please guide us what will be the copper wire size for installing 5 cassate AC of 4ton each.
regards
Dear Sir,
Can you please suggest the cable size/dia as per following.
+ Transformer. 1500kva
+ distance from transformer to plant. 1800 meters
+ ultimate consumption, 250kv..
thanks and best regards.
If you have a gauge 4 stranded or solid copper wire, how do you calculate its quantity equivalent of a lesser gauge stranded or solid wire? If I were to strand 10 gauge copper wire (solid or stranded), how many do I need to equal 4 gauge copper wire? Does this calculator able to do this? Is this even possible? I am guessing calculate the total resistance per linear foot and make it equal.
Sir iam electrician but not iti chartifacet.all work exp.electrical.and plambing work