# How to Calculate/Find the Rating of Transformer in kVA (Single Phase and Three Phase)?

**Calculate & Find the Rating of Single Phase & Three Phase Transformers in kVA**

We know that, Transformer always rated in kVA. Below are the two simple formulas to find the** rating of Single phase and Three phase Transformers**.

**Find Rating of Single Phase Transformer**

Rating of Single Phase Transformer:

P = V x I.

**Rating of a single phase transformer in kVA**

kVA= (V x I) / 1000

**Rating of a Three Phase Transformer**

Rating of a Three Phase Transformer:

P = √3. V x I

**Rating of a Three phase transformer in kVA**

kVA = (√3. V x I) /1000

But Wait, A question is raised here… Look at the General nameplate rating of a 100kVAtransformer.

Did you notice something????Anyway, I don’t care what is your answer 😉 but lets me try to explain.

Here is the **rating of Transformer is 100kVA**.

But Primary Voltages or High Voltages (H.V) is 11000 V = 11kV.

And Primary Current on High Voltage side is 5.25 Amperes.

Also Secondary voltages or Low Voltages (L.V) is 415 Volts

And Secondary Current (Current on Low voltages side) is 139.1 Amperes.

In simple words,

Transformer rating in kVA = 100 kVA

Primary Voltages = 11000 = 11kV

Primary Current = 5.25 A

Secondary Voltages = 415V

Secondary Current = 139.1 Amperes.

Now calculate for the rating of transformer according to

P=V x I (Primary voltage x primary current)

P = 11000V x 5.25A = 57,750 VA = **57.75kVA**

Or P = V x I (Secondary voltages x Secondary Current)

P= 415V x 139.1A = 57,726 VA = **57.72kVA**

Once again, we noticed that the rating of Transformer (on Nameplate) is **100kVA** but according to calculation…it comes about **57kVA**…

The difference comes due to ignorance of that we used single phase formula instead of three phase formula.

Now try with this formula

P = √3 x V x I

P=√3 Vx I (Primary voltage x primary current)

P =√3 x 11000V x 5.25A = 1.732 x 11000V x 5.25A = 100,025 VA = **100kVA**

Or P = √3 x V x I (Secondary voltages x Secondary Current)

P= √3 x 415V x 139.1A = 1.732 x 415V x 139.1A= 99,985 VA = **99.98kVA**

**Consider** the (next) following example.

Voltage (Line to line) =** 208 V**.

Current (Line Current) = **139 A**

Now rating of the three phase transformer

P = √3 x V x I

P = √3 x 208 x 139A = 1.732 x 208 x 139

P = 50077 VA = **50kVA**

Note: This post has been made on the request of our Page fan Anil Vijay.

Why is transformer rating always written in KVA? We know that the unit of Power is Watt. then why don't we write transformer rating in Watts?

Dear Mukesh Khatri@ Read This Article Why Transformer rating in kVA and not in kW?

Both consider rating important only its concerned the power factor fluactuation to be maltiply.

english RIP

So what!! at least he can communicate in another lang. other than his own.

Try to be technical John.

just because we don’t know that this transformer where use there are three type of load no:1 resistive load no:2 capacitive load no:3 inductive load if transformer not in KVA you can not use all three type of load so we make transformer in KVA so that we can use in three type of load.

Motor bhi inductive resistive and capacitive load pe chalti hai to uska rating KW me kyu hota hai

Very useful post

When input power in electrical and output is also in electrical the the device , transformer, generator etc capacity are measured in kVA , but when input power is electrical and output is mechanical energy like motors its capacity is measured in ke.

The transformer losses are mainly depend in voltage and current so the voltage=v ,current,=A and the rating in terms of transformer is kilobits so we can say transformer rating in kvA

The two types of transformer are core loss and ohmic losses.<br />The core loss depends on transformer voltage and ohmic loss depends on transformer current.As these losses depends on transformer voltage and current and are almost unaffected by the load pf, transformer rated output is expressed in VA or in KVa.

because the power factor of the load is not known so transformer rating is given in KVA

Because it has three resins:

1. Transformer winding consists Copper and copper losses are occurs in winding due to current(I).

2. Transformer core obliviously made by Ferromagnetic material and core losses are occurs in core due to voltage(V).

3. Transformer transmit high electrical energy so reduce the unite of voltages level engineers used kilo(K) unit for transformer.

So, that transformer rated in KVA mean Kilo volt Ampere.

Sincerely,

Why does my .5 kva transformer say its rated for 31.25 amps but wen i try and size my transformer needed it says i need 7.68 kVa transformer for 32 amps at 227 volts

cz transformer rating depends on temprateure and tempreture is depneds on loss

as you know that their is two type of loss copper and iron

copper>> Current (A)

Iron>> Volt(V)

So if it depends of powe then we can say that it will in in KW but it denpends on Loss So we used in KVA

transformer rating is related to its losses. there are copper loss and core loss in trasformr. copper loss is depends on current and core loss is depends on voltge,so the rating of transformer is said to be the product of voltage and current. VA OR KVA

Thanks

dear in last consideration u shows that line to line volts is 208V then after calculation over value is came 50 KVA but actual value is 100 KVA have. plz Kindly explain it

Dear Waqas Ahmed<br />Here are two examples.<br />The first one is for 100kVA which shown in the image.<br />The Second one is for 50kVA (where line to line voltage is 208V)

Your article looks great!Thanks for you sharing. I love it. High Voltage Transformers

thanks teacher

If we dont know the line current,how 2 calculate the rating?

It is already given on every transformer's nameplate

This system arrangement is very common, both at the utilization level as 480 Y/277 V and 208 Y/120 V, and also<br />on most utility distribution systems.

kW=kva×pf<br />is it right?

Yes it is 100% right. When considering the apparent power we also considered the effect of inductor and capacitor which always will be minimized by using power factor correction technique. Points to be remembered: KVA is always greater then KW because KW only have the effect of resistor. KVA=KW if and only if the power factor is one so the load is pure

sir could u explain DYn-11…..

Wait for the upcoming posts… Thanks

http://en.m.wikipedia.org/wiki/Vector_group

The “D” indicates that this is a three phase transformer and the primary is connected in DELTA then the “y” indicates that the secondary is connected in STAR connection “N” indicates that the star point is taken out from the transformer and is known as Neutral . The “11” indicates that the vector of secondary voltage is lagging by 30 degrees from the vector of primary voltage RAJ LAHARE

IM ALSO INFORMED BY THESE EXPLANATION THANKS.

Hello Sir, Can u explain why in transformer,the power factor is not considering.? And why in others.?

Correct me if I'm wrong ' The power factor is determined by the load, not the transformer. The PF on the load side of the transformer will be the same as it is on the primary, except at very light loads where the magnetizing current could have some effect. Having said that, the impedance in the primary circuit could effect the PF of the system. In other words, for a given load (with

hi sir, how do the transformer designer calculate the turns, emf, loss, flux, area if we say we need1600KVA

you can find the loss with the help of open circuit(eddy current and hysterisis) and short circuit test(copper loss) and other parameter can also be calculated with these test.

hi sir, how does transformer designer calculate flux, emf, loss, turns if v just say the rating eg,1600Kva if u reply with a example calculation it will be comfortable

Hi Sir, what size transformer do I need for 5A,230V Load?

Hi Sir, what size transformer do I need for 5A,230V Load?

dear 220kv/500kv transmission poll install in the forest.and we don't know the load and the production side.so tell the method of load and production identification?<br />

hi sir, i want to design a 500VA rating of transformer.but i dont understand how to select the v/g & c/n value? and no. of turn on each side of transformer?<br />pls kindely rply me<br />

Sir ,why we dont consider power factor for transfrmer but for generator or motor?

Sir ,why we dont consider power factor for transfrmer but for generator or motor

Dear Sir, I want to know about how to select step down transformer rating. 415/230V and VA rating. ..?..I mean how we can be calculated. .based on the which factors. .

Can you explain me how to calculate the output current of 3 phase trasformer? can you explain me with formula?

Sir, how to calculate the rating of VCB for HT side,ACB for LT side and what are the CT meter ratio required,the load the shop is 410 kw ( 500 kva transformer)

high sir i got one assignment from my teacher Vo=0 to 15 volts and iL=load current is 3 and design the transformer

Any one have complete designing calculation of distribution transformer of 25KVA

Can any one explains about Cable cross bonding and transposition clearly..

Thanks in advance.

Sk Anwar Basha.

P unit is KW

S unit is kVA, MVA.

P unit is kVAR.

Why you write P (kVA)? Please explain? Do you know Transformer formula? S2 = P2 + Q2 ?

Sorry, Q unit is kVAR.

yes oyu correctly htk…i agree..

send me star-delta starter control wiring diagram with remote control &indication wiring.

calculation how much kvar capacitor will connected to100hp load

is there another reason for why transformer rating in KVA and what is the necessity of power factor

Hi Sir,

could you please explain me how to calculate knee point voltage Vk of a CT, say 132/33kv, 30 MVA Transformer feeder. %z= 8.5

Sir 500VA Control transformer take how many ampere and how to calculate it????

VA = Voltage x Amps for single phase

or

KVA = Voltage x Amps for single phase/1000

VA = square root of 3 x Voltage x Amps for three phase

or

KVA = square root of 3 x Voltage x Amps for three phase/1000

respected sir:

if we make a transformar that have;

pri: 230v

sec: 12v and 35am

how much turns required for this

if we use the core size(2*3) tell me with exemple

Dear sir I am facing a problem with electricity board of Talangan State.

Kindly guide me to come out with this problem,

I had applied 18 nos 5kw each domastic services & 2nos each 15&20kw commercial services total load 125 kW for my Residential/Commercial Apartment, department asking me for 160kva but I’m arguing for 100kva. my calculation is for domestic 18×05=90KW ÷ 2 ÷ 0.9 = 50,

commercial 15+20=35KW ÷ 1.5 ÷ 0.9 =25.92,

Total KVA 75.92

The formula which I mention is belongs TSSPDCL.

Why should I take 160kva if 100 kva is sufficient to me.

Dear sir I am waiting for your replay for this particular formula if I get any book or however you please guide me

Thank you

sir as in this case you showed us max load of transformer 100 kva but i want to ask you how much load it will support actually on site. what is the safety factor or service factor of transformer.lets suppose we have a load of 1200 kva now tell me appropriate size of transformer for this load thanks

Dear, The proper load of transformer is not defined (it may inductive, capacitive, resistive or max load…Thats why it is rated in kVA insted or kW.

hi sir can show me how to ansenser this pleas Work out the transformer primary and secondary currents assuming an 11kV/400-230V, 3-phase, 50

Hz supply transformer and suggest suitable types and ratings for the primary and secondary protecti

In a numerical probem, transformer rating is given as 220/13.8 KV. I want to know which is primary and which is its secondary?

In your case, the transformer rating looks like, 220kV is primary while 13.8kV is secondary… (In case of Step down i.e. distribution side transformer…

dear i am asking for load .how much kva rating of transformer for 200kva load

The capacity of transformer required for 200 Kva load can be correctly ascertained only after receiving the individual loading pattern . For example the total load of 200 Kva from small motors like 5 , 10 HP ( KVA ) each the transformer of 200 KVA only is enough.But If a individual load is more tha 150 KVA You will need at least 300 KVA capacity transformer. RAJ LAHARE

Hi ,

I am having a motor 460V, 10HP , It will be great if you could please let me know the rating of the transformer which I need to use for connecting it to our supply voltage of 600V. I would also like to know the steps involved in calculating the rating of step down transformers for motors.

Jacob

13.8kv is primary and 220/380 is secondry

Hello, I am facing a little problem with transformer calculations.

I have 3ph 600V 200A feed , and trying to figure out size of transf. for 208V 1phase, there is many explanations but none on 3phase to single phase calculation. Can you help me please.

Regards

Dejan

A contractor has supplied a transformer 11/0.433 KV, 160 KVA . I suspect that the transformer is not of that rating. How can I check / Test this

the input voltage rating need not be be exceeded nor should the output current(amp) but lets say the transformer is rated at input of 11 kv with an output of 235 and you have 5.5 kv coming in and you want 120 this is what you should expect 118 this would be fine i did not go into current ratings but i suspect this more or less what your contractor did your transformer will have costed a bit more but will last allot longer likely for a hospital or something that needs a high reliability

We have been supplied a Transformer of 160 KVA 11/0.433 rating. How we can check / test that the transformer is of Given rating ?

for 600 KVA transformer what will be the line current or individual phase current?

For proper answer you will have to give following additional information. Whether the transformer is single phase or 3 phase. What is the primary and secondary voltage Please clarify .

Dear Nirmal, This is not reply to my query.Your answer gives the loading on the transformer and NOT the Rating / capacity of transformer.

How can i calculate transformer capacity with out looking at main plate of the transformer.

Thank you to anil and vijay sir.

The formula will give the load in VA or KVA on the single phase transformer and can not give the capacity of the transformer. The Capacity means How much load can be put on the said transformer without over heating and with voltage drop within limit .Wish proper guidance.

how can we determine the KVA rating of a transformer from test

My query is for determining the capacity

What do you mean by Transformer Capacity?

My query is for determining the capacity of a available transformer.But I am not getting any proper answer to my query.

What do you mean by Transformer Capacity? Do you want to know about the weight or T/F or Rating of Transformer?

Sir, Can you tell me that what is T/F?

T/F is the short form of TRANSFORMER.

daer all The word Capacity is very clear. It can never be the weight. The capacity means for a given transformer how much electrical load can be put on this transformer. Say for a transformer of 230 / 12 volts and 60 VA capacity ( Single phase) The max load can be 5 Amps on 12 V side if the load is exceeded the transformer will get overheated and may burn off. So if I want to verify this capacity , what is the laboratory method ? My origional question was regarding a transformer supplied by a contractor saying 160 KVA capacity but at about just 120 kva load this transformer gets over heated than the specified temperature. So the query. RAJ LAHARE

160kVA Transformer Capacity overheated on 120kVA load? There may be different factors.

Did you check the Transformer power factor (As improved P.F increased the T/F Capacity as well) or did you verify the proper cooling of the transformer?

In your case, Transformer Load capacity will be considered as Transformer Rating in VA or kVA.

Also, The Transformer load capacity is the Rating of the Transformer x P.f.

Dear Sir,

I specifically say that the load is 120 KVA and not KW so the question of Power factor do not come in picture. Still to communicate that the PF is 0.99 . The Transformer is outdoors like any other transformers so cooling etc do not come in picture . I suspect that the supplier must have supplied lower capacity transformer with rating plate of 160 Kva and I want to test / investigate this . RAJ LAHARE

For This, You need to know the two pieces of information

1. the load line-to-line voltage (V)

2. the maximum load phase current (I)

Where

kVA Capacity = ( √3 x V x I x cosΦ ) / 1000

Do this simple calculation then

Or You need This tool to do the job.

As per basics of transformer , The power capacity of transformer ( VA ) is based on the cross section and the permeability of the transformer core. Then the voltage is based on the Number of Turns . Based on the Voltage and the VA capacity the current is arrived at and then only considering standard losses the current is calculated which inturn will give the cross section of the winding conductor. Here the transformer is already received and is sealed. I know very well to ascertain the capacity by opening the transformer and then measuring the Core area, primary and secondary winding cross section area and then measuring number of turns each of primary and secondary. BUT I DO NOT WANT TO DO ALL THIS EXERCISE AND WANT TO CHECK THE CAPACITY OF SUPPLIED TRANSFORMER WITHOUT OPENING THE TRANSFORMER. I HOPE AT LEAST WITH ALL THIS CLARIFICATION I WILL GET PROPER GUIDANCE . I ONCE AGAIN SAY THAT I DOUBT ABOUT THE SUPPLIED TRANSFORMER IS NOT OF ORDERED ( 160 kva) CAPACITY. RAJ LAHARE

Dear Sir,

I need complete calculation with formula. Now my doubt is I have total 125kw load so how much rating of transformer I require. please inform it’s urgent to me.

kW = kVA x Cos(Ø) = Where Cos(Ø) = Pf…

Now Transformer rating in kVA = kW/Cos(Ø)

Now put your actual power factor (for instance pf=09)

kVA = 125kW/0.9

kVA = 139kVA

for additional load in the future… 150kVA would be better than.. Thanks

Dear Sudarshan,

In my earlier mail I had given a comment and also suggested that the capacity of transformer is dependent on the max individual load so If you can give your list of 125 KW load the correct capacity can be calculated. RAJ LAHAREthe

Its really satisfaction to concept thakyou sir..

Sir why KVA is divided by 1000

It is actually VA (Volt-Ampere) .. Instead of 1000VA, We divide it by 1000, So that, It becomes 1kVA, where k = 1000.

who is the owner of this website ?

whoever he is, a simply genius of electrical engineering. simply awesome.

Thanks for appreciation … 🙂

Draw a schematic single line diagram for the distribution of the complex in question, showing where

appropriate the transformer, generating set/sets and UPS systems

for a 3 phase transformer, is there always line to line voltage written on name plate for star connection?

Yes, for three phase transformers the voltage given on name plate is phase to phase NO LOAD that is open circuit voltage. On load ,depending on the impedance transformer the secondary voltage drops down to some extent. RAJ LAHARE

Thanks..@RAJ LAHARE

It is really good job done by this website thanking you.

HOW TO Convart H.T amper to L.T Amper..formola

Dear Sir

Suppose someone have given transformer capacity, LV side voltage, HV voltage and believe power factor is 1, than how to calculate LV site current capacity and Hv side current capacity?

Please awaiting for kind reply.

For this additional DATA is required 1) Whether the transformer is single phase or poly phase 2) If poly phase what is vector group on primary and secondary side then only correct solution can be given . In any query if correct input is given the answers can be faster. RAJ LAHARE

Primary side voltage is 230 v, secondary side voltage is 50 vhow to calculate KVA..This is a old transformer no name plate details in this transformer

Dear Chokklingam,

As per your query this seems to be single phase transformer, There is no name plate as per your statement. Can you send the details as the cross section area of the core and the material used for the core. further whether the transformer is core type or shell type ,then the rating can be calculated. RAJ LAHARE

Hey transfermoer rating in kVA

Dear Harish ,

Your query is not clear so no comment can be given RAJ LAHARE

500 kva tarsformer fuse range

For deciding the fuse rating we must know the voltage ratio of the transformer And the full load current is always written on the rating plate. For the 500 KVA 11 KV /0.433 KV three phase DYn11 Transformer HV Full load current is @ 26.65 Amps and Lv side current is @ 667.5 Amps. RAJ LAHARE

i want to select frequency drive for transformer application.transformer rating is 500 va .what will be rating of drive pls help

Dear Bhushan,

It may be kept in mind that the Transformers are the sours of electrical energy from the system at given voltage. And the basic design of the transformers are related with the frequency, wave form, Permeability of the core and the voltage, And the Drives are designed for limiting the inrush currents of the motors Say it is a current control device. so there no meaning in design of frequency drive for a transformer. RAJ LAHARE

i have a microwave transformer that i want to reuse as a welder i have 56 windings on the primary of 12 gauge the core is laminated soft iron in the shape of a box with a bar that divides the primary and secondary over dimensions 4.25 x 6.25 x 2.25 with core wall thickness of 3/4 and the dividing wall between the coils is 5/8 of in square

i was thinking of using some simple 4 gauge thwn wire covered in a high temp sleeve as the secondary cooling it off with a 200 cfm fan while placed in a metal case that is just over 1/4 in wider on 2 sides and above and front and back is also 1/2 in biggerbellow 1/2 in the fan will make a tight seal i am wanting to do resistance spot welding any advice on changes in design and duty cycle ratings

Dear Tom, When You give dimenssions You are also expected to give the Units such as whether the measurements are in MM or CM or Inches..Secondly what is the cross section Area of the CORE And what is rated Primary Voltage and secondary voltage of this transformer. On hearing this solution can be suggested. Can You please send the photograph of your existing transformer ? RAJ LAHARE

Dear Tom, This is NOT technical reply to my Query. I will like to have perfect TECHNICAL solution to my query. RAJ LAHARE

Earting & Transformer

Dear Jayawanta,

Your query is not clear raj lahare

Hello i want to know HV and LV coil resiatance and inductance values of 11kV/440V rating 100kVA transformer

Dear Mahantosh,

Refer IS 2026 and You will get all the details RAJ LAHARE

How do I calculate the fuse rating of a power supply circuit with 500VA, 220V AC/ 15V AC step-down transformer, if after rectification, filtration/smoothening, and 12V DC regulation; the load is a purely resistive load of 100watts, 12V DC. Thanks.

thanks for the content because i really liked it

Dear Tony, Your transformer is 500 VA with 220 volts promary so the primary fuse rating will be 2.27 Amps say 2 Amps. Now you are using resistive load at 12 volts DC and 100 watts so your secondary side current willbe 8.33 Amps so you may use 8 Amps fuse. For full load of 500 watts at 12 volts the current will be approx 41 Amps so the fuse required will be 40 Amps. RAJ LAHARE

hi Raj,

If the load for a building 39kw 3/phase and 10kw for s/phase.

Please give me the formula for total load and required transformer rating.

thanks

Dear Jan,

For technically correct calculation of the requirement of transformer some additional DATA will be required that is The details of 39 KW 3 phase load bASICALY what is the highest idivisual load.And what is the source voltage. Please. RAJ LAHARE

how to design transformer increas or decraes

Dear Kashif Khan ,

Your question is not clear.

how to find primary and secondary amp of a 1500 kva transformer (11kv/400v). Pls reply

Dear jkjk,

As we know Kva = root 3* V * I *1000 so for your problem

1500 = 1.7321 * 11000 * I so

I = 1500* 1000 /1,7321/11000

= 78.72 Amps

You may caThis will be full load current of transformer Now You can calculate current on 400 volts side.

Remember 11 KV voltage is phase to phase voltage.If find difficult may ask again .

I agree with Mr. HTK. The KVA should be for appearance power S NOT in P active power, however if you want to calculate in P active power, in this case you have to take into consideration the power factor and the result will be in KW not in KVA.

I have a power system,in the following order, with a source of 132kV, 2No, 140 MVA, 132/33kV transformers, 33kV Bus, 8 transformers of 1.6MVA, 33Kv/415V, 8 loads of 0.8 MW, PF=0.9, connected to the transformers at 415V side. 2 transformers of 50MVA, 33kV/11kV, connected from the 33kV bus to 11kV bus, 4 transformers of 5 MVA, 11kV/3.3kV, to which 4 loads of 2.5 MW are connected with PF=0.9, 4 transformers of 2MVA, 11kV/415V, to which 4 loads of 1MW each are connected with PF=0.9.

My question is, what is the total connected load at 132kV receiving point, do we need to consider the transformers as load, or just the main load are enough??

I’m giving the list of transformers and load again,

Transformers: 140MVA (2No), 50MVA (2No), 1.6MVA (8No), 5MVA (4No), 2MVA (4No)

Loads: 0.8MW (8No), 2.5MW (4No), 1MW (4No), all at POWER FACTOR = 0.9

Please help me calculate the total load at 132kV receiving point.

How to calculate the total load received at the source point? suppose I have the following in my power system:

Transformers: 140 MVA, 132/33KV (2 NO). 50MVA, 33/11KV (2 NO). 1.6MVA, 33KV/415V (8 NO). 5MVA, 11/3.3KV (4 NO). 2MVA, 11KV/415V (4 NO)

LOADS: 0.8 MW, PF=0.9 (8 NO), 2.5MW, PF=0.9 (4 NO). 1MW, PF=0.9 (4 NO).

VARIABLE SPEED DRIVE: VSD1- 18.2 MW, VSD2 – 16.3 MW

Receiving point:- 132kV source generator

Dear Abdullah,

Coinsidently Similar question is asked by Mr, Thaamir, For exact calculations of this type You are also expected to give additional information such as 1) whether all the transformers of same voltage rating are connected in parallel or are separate. 2) Percentage impedance of each transformer. How ever roughly the Total load on 132 System will be Approximately 25.47 MVA considering standard Transformation loss of 5 % at each level. If You can give thiven. RAJ LAHAREe clarification of above 2 points still correct answer can be g

Dear Mr.Raj,

1) 1.6 MVA transformers are connected in parallel in pairs. there are 8 such transformers, so there are 4 pairs. similarly, two 5MVA are connected in parallel, so there are 2 pairs. Similarly, two 2MVA transformers are connected in parallel, so there are 2 pairs. the 140 MVA and 50 MVA transformers are connected separately.

2) the percentage impedance are:

140 MVA TF, Z%=12.5

50 MVA TF, Z%=12.5

1.6 MVA TF, Z%= 6

2 MVA TF, Z%= 6

5 MVA TF, Z%= 8

Thank you in advance for your timely help, if you give your email id, i can send you my system, so that it will be clear to you.

Load is calculated in ampere or megawatt not in MVA. For example, if you are calculating a load on 33kv, the total current flow on it is the load. Let say 50A. Then , if you want to convert the load to megawatt, you divide 50A by 20. If it is on 11kv, the 50A load will be converted to megawatt by dividing it by 60. If it is on 132kv, the 50A load will be converted to megawatt by dividing it by 5.

Hi Abdullah,

Coming to your question, first of all, you have to consider transformation ratio of your voltage level(i.e 132kv/11kv,132kv/33kv,33kv/11kv), then, with respect to my recent post, convert all the megawatt loads to current loads(i.e the megawatt loads for 11kv convert them to current loads by multiplying the total sum by 60, while those of 33kv megawatt loads will be also converted to current loads by multiplying the total sum by 20). After that, divide the current converted load of 33kv by 4 to get the current load on the 132kv and divide the converted current load of 11kkv by 12 to get the current load on the 132kv. Then, sum your answers to get the total current load of the 132kv. To convert it to megawatt load, divide the 132kv current load by 5. Thanks.

dear all,

tel me some explanation about leakage current in 100kVA distribution transformer and what is the maximum leakage current allowable in transformer

any one pls..

Dear Gubendiran, Please refer to ISS 2026 and ISS 1180. You will get all the information. These ISS publications are available on internet. raj lahare

thanks for the reply sir..

i seen the both standards there are no specific value of leakage current.i want standard value of specific leakage current.standards only says how to find and measure leakage currents.i think 100mA for 100kVA distribution but how???

dear sir,

Thanks for the reply.

i seen both standards there are no permissible or maximum allowable leakage current in directly mention.could you please answer me.

My power transformer is 10 MVA capacity what is the Maximum Amps load can be connect in 33 kv, 11kv or 415 V, with formula

Hi Akhatar Ali,

For 33KV: 10MVA/1.73*33KV=10*1000000VA/1.73*33*1000V=10000A/1.73*33= Simply further

For 11KV: 10MVA/1.73*11KV… simply further.

Note: 1.73 is gotten from Root three (root 3)

Take care!

Dear Akhatar Ali.

As the thumb Rule the full load current on 33 KV side for 10 MVA load is 175 Amps. for 11 KV it will be 525 Amps. and for LT 440 volts it will be approx 13125 Amps. RAJ LAHARE

Thanks a tonne!

pls , what is responsible for high voltage in a distribution transfomer, 11/.415kv, 100kVA after one of the phases coil that got burnt, has just been replaced

how do i determine the correct rating of fuse of 11/.415kv,500KVA transformer, both primary and secondary side

You mentioned Line – Line voltage at bottom of the article.. But you’ve done as 208V for 3-Ph Instead of 415V.

for 415V;

P= 1.732 X 415 X 139.1 = 99982 VA = 99.98 KVA

So Please correct it.

Thanks

Best Regards.

The second example for US. There are 208V in three Phase instead of 415 like UK and Asia.

I have a transformer with 110/220 input primary,secondary has:0v 33v,0v 13v,27v 0v 27v,9v 0v 9v.The CD player consumption is 25watts.How do I get the amps from the secondary?.Do I have to divide with 25watts with all of the secondary winding?.

Dear sir ,

What you write here for calculation of power in single and three phase transformer p= √3×v×I is this is right because we know active power denotation is by s.

So please correct the formula

For single phase

S= v×I

Three phase

S=√3xvxI

Thanks & regards

Indra naryan

Ind441@gmail.com

Apparent power denotation by s in kvA so calculation of power in kva we have to denote s =√3xvxI in three phase transformer

Not p = √3xvxI

So we have to correct the formula

Regards

I have a 3 phase 75 KVA transformer being fed from a 80 KW standby diesel. the transformer is reverse fed…that is the diesel is putting out 208 volts delta 125 amp on the high voltage side and the low side it is 3 phase 4 wire at 600/347 volts. My question is ..what amperage could I get from the 600/347 side ?

Dear Bill, Your question is rather confusing, for Better and correct technical answer please send the rating plate details of both the, transformer and the Diesel Generator. RAJ LAHARE

Dear Bill,

Your query is rather confusing. Please give the Rating plate details of both, the Transformer and the Generator, If possible the schematic diagram of the system so That better answer can be given. RAJ LAHARE

Awesome, very well written article. Many important points are covered here.

Unfortunately the queries are not Technically perfect, rather they are vague. RAJ LAHARE

i have a question regarding transformer

transformer having primary voltage of 11000 v ,than why the fuse of 5A is used ?

You are doing great job sir. Keep it up.

HELP ME OUT, why is it that 12v from electricity can electrocute but same 12v from car battery can not be electrocuted

Dear All , If you check the second example provided that states 50KVA transformer and the voltage taken is 208 Volts is probably not correct . The reason why i am saying is there is no 50KVA transformer with a voltage of 208 Volts. 208Volts is a single phase voltage as per rules of SEC and U.S Standards. 50KVA is a three phase not a single phase .

Please provide me star-delta starter control wiring diagram with remote control &indication wiring.

I must confess that this is a good place to be

I was able to carry out short circuit Voltage Impedance test on a 7.5MVA, 33/11KVA transformer. From the test I was able to ascertain the actual impedance of the transformer using, Measured Sec. Voltage/transformer sec. voltage X Transformer Sec. Current/ Measured Secondary Current X 100%. Using the same test result, One should be able to determine the Rating(Capacity of the transformer). Can anybody help with the formula to use for this calculation?. Thank you

I would like some technical assistance regarding transformer. My question is i have a transformer of 2000kva, Its voltage ratio is 6/0.415 KV now i want to use this transformer on 6.6KV instead on 6KV. What will be the impact on transformer and can we use it on continuous operation. Secondly can we use it by changing its tap on 6.6kv. Kindly assist me. Thanx.

Dear Mr. Mukhtar,

Send the complete Name Plate details of Your Transformer so That Correct technical Guidance can be given. You May mail the same directly to me . “rajlahare@gmail.com”

Dear Mukhtar,

You Know that the The Rating of Primary Voltage is of most importance for the health of transformer and the same should never be increased. with 6.0 KV rating of transformer and If you feed 6.6 KV to it “about 10 % higher” the transformer will FAIL. Further your output voltage will also be 415 + 41.5 =456.5 volts this will damage your Equipment connected on LV side of transformer. So for proper Guidance you may send Transformer”s number plate/ name plate details directly to me “rajlahare@gmail .com “

are the formulas same for step up and step down transformer? in the name plate pic how come we know it is step up or step down?

On the transformer name plate, they clearly mentioned the primary and secondary (HV & LV) Voltages. If Primary (HV) Are higher then the LV, It is Step down and vice versa.

There are always minimum 2 windings for a transformer. 1 primery winding and 2 secondary winding. If voltage of primery winding is more than that of secondary winding then the transformer is step down type.

i’m having troubles determining which of the stated transformers have greater losses: a 33kv/415v or a 11kv/415v

What is the rating of vcb for 500 kVA transformer.

Sir please specify how to calculate indoor VCB size according to transformer????

Very fascinating facts about generating Power, My wish is also to have sustainable Power generating systems which is eco friendly and safe for Our Planet and also can be there for the future generations,generating Power is the way to go, but also be more responsible in sustaining it. Thank you for the space to share, wishing you the best of luck, CHEEEERS

Hello. Im try to understand the behavior of a transformer 11kv/415v. When : 1. Its dedicated to a single consumer ( quarry and big industrial plant) 2. Its total power its smaller than the consumer needs( the transformer its 1000kva and the consumer typically needs its 1200kva) The loads are instantly dramatically change because of heavy loads machines( rocks crushers) and the plenty of smaller motors. Thanks and i hope read an article about that. P. S. I can give more data and power quality measurements about the occasions.