**Star Connection (Y)**

In this kind of interconnection, the starting ends or finishing ends (Similar ends) of three coils are connected together to form the neutral point. Or

Star Connection is obtained by connecting together similar ends of the three coils, either “Starting” or “finishing”. The other ends are joined to the line wires. The common point is called the neutral or Star Point, which is represented by N. (As shown in fig 1)

Star Connection is also called Three Phase 4 wires (3-Phase, 4-Wires) system.

If a balance symmetrical load is connected across three phase voltage system in parallel, then the three currents will flow in neutral wire which quantities would be same, but they would be differ by 120° (out of phase), hence the vector sum of these three currents = 0. i.e.

I

_{R}+ I_{Y}+ I_{B}= 0 ……………. VictoriallyRead More : Phase Current Values in 3-Phase Current

The voltage between any two terminals or Voltage between Line and Neutral (Star Point) is called Phase voltage or Star voltage. And the voltage between two Lines is called Line to Line Voltage or Line Voltage.

*Click image to enlarge*

**1. Line Voltages and Phase Voltages in Star Connection**

We know that the Line Voltage between Line 1 and Line 2 (from fig 3a) is

V

_{RY}= V_{R}– V_{Y}…. (Vector Difference)Thus, to find vector of V

_{RY}, increase the Vector of V_{Y}in reverse direction as shown in the dotted form in the below fig 2. Similarly, on the both ends of vector V_{R}and Vector V_{Y}, make perpendicular dotted lines which look like a parallelogram as shown in fig (2). The Diagonal line which divides the parallelogram into two parts, showing the value of V_{RY}. The angle between V_{Y}and V_{R}vectors is 60°.Hence, if V

_{R}= V_{Y}= V_{B}= V_{PH}, thenV

_{RY }= 2 x V_{PH}x Cos (60°/2)= 2 x V

_{PH}x Cos 30°= 2 x V

_{PH}x (√3/2) …… Since Cos 30° = √3/2= √3 V

_{PH}Similarly,

V

_{YB }= V_{Y}– V_{B }= √3 V

_{PH}And

V

_{BR}= V_{B}– V_{R}= √3 V

_{PH}Hence, it is proved that V

_{RY}= V_{YB}= V_{BR}is line voltages V_{L }in Star Connection, Therefore, in Star Connection;V

_{L}= √3 V_{PH}or V_{L}= √3 E_{PH}It is seen from the fig 2 that;

- Line voltages are 120° apart from each other
- Line voltages are 30° leading from the corresponding phase voltages
- The angle Ф between line currents and respective line voltages are (30°+Ф), i.e. each line current is lagging (30°+Ф) from the corresponding line voltage.

**2. Line Currents and Phase Currents in Star Connection**

It is seen from the fig (3a) that each line is in series with individual phase winding, therefore, the value of line current is same as in Phase windings to which the line is connected. i.e.;

- Current in Line 1 = I
_{R} - Current in Line 2 = I
_{Y} - Current in Line 3 = I
_{B}

Since, the flowing currents in all three lines are same, and the individual current in each line is equal to the corresponding phase current, therefore;

I

_{R}= I_{Y}= I_{B}= I_{PH}…. The phase currentLine Current = Phase Current

I

_{L }= I_{PH}In simple words, the value of Line Current and Phase Current is same in Star Connection.

*Click image to enlarge*

In a three phase AC circuit, the total True or Active power is the sum of the three phase power. Or the sum of the all three phase powers is the Total Active or True Power.

Hence, total active or true power in a three phase AC system;

Total True or Active Power = 3 Phase Power

Or

P = 3 x V

_{PH x }I_{PH}x CosФ ….. Eq … (1)**Good to Know:**Where Cos Φ = Power factor = the phase angle between Phase Voltage and Phase Current and not between Line current and line voltage.

We know that the values of Phase Current and Phase Voltage in Star Connection;

I

_{L }= I_{PH}V

Putting these values in power eq……. (1)

P = 3 x (V

P = √3 x√3 x (V

P = √3 x V

_{PH}= V_{L}/√3 ….. (From V_{L}= √3 V_{PH})Putting these values in power eq……. (1)

P = 3 x (V

_{L}/√3) x I_{L}x CosФ …….…. (V_{PH}= V_{L}/√3)P = √3 x√3 x (V

_{L}/√3) x I_{L}x CosФ ….… {3 = √3x√3}P = √3 x V

_{L}x I_{L}x CosФHence proved;

Power in Star Connection,

P = 3 x V

_{PH x }I_{PH}x CosФ orP = √3 x V

_{L}x I_{L}x CosФSimilarly,

Total Reactive Power = Q = √3 x V

_{L}x I_{L}x SinФ**Good to know**: Reactive Power of Inductive coil is taken as Positive (+) and that of a Capacitor as Negative (-).

Also, the total apparent power of the three phases

Total Apparent Power = S = √3 x V

_{L}x I_{L}Or, S = √ (P

^{2}+ Q^{2})**Also Read :**

**JLCPCB - Prototype PCBs for $2 + Free Shipping on First Order**

China's Largest PCB Prototype Manufacturer, with 290,000+ Customers & 8,000+ Orders Per Day

10 PCBs Price: $2 for 2-layer, $15 for 4-layer, $74 for 6-layer

This is the best way to learn. I have learn a lot of topics

Very helpful artical..it explains the topic very clearly…

Thanks..