Automatic Star / Delta (Y-Δ) Starter with Timer for 3-Phase Motor
The Star-Delta (Y-Δ) 3-phase Motor Starting Method by Automatic star-delta starter with Timer
Table of Contents
Table of Contents
Automatic Star Delta Starter with Timer Wiring & Installation Diagram
Explanation of the working and operation of Star Delta Automatic Starter with Timer Wiring Installation:
From the left you have the main contactor with the pneumatic timer because your main contactor is always energized, in the Middle you have the Delta contactor with a thermal overload for motor protection in case the motor exceeds the ampere rating set on the thermal overload, on the right you have the Star contactor which is the first contactor to be energized with the main contactor then when the timer reaches its time limit the Star contactor de-energizes and the Delta contactor energizes and the Motor is running at full load.
Related Motor Control & Power Diagram
- Three Phase Motor Connection STAR/DELTA Without Timer Power & Control Diagrams
- Control 3-Phase Motor from more than Two buttons Power & Control Diagrams
Operation & Working Principle of Star Delta Automatic Starter
- Contactor coil C3 and timer coil (I1) is energized at once and the motor winding then connected in Star. When C3 is energized, its auxiliary open links will be closed and vice versa (i.e. close links would be open). Thus C1 Contactor is also energized and Three Phase Supply will reach to the motor. Since winding is connected in Star, hence each phase will get √3 times less than the line voltage i.e. 230V. Hence Motor starts safely.
- The close contact of C3 in the Delta line opens because of which there would be no chance of activation of contactor 2 (C2) .
- After leaving the push button, Timer coil and coil 3 will receive a supply through Timer contact (Ia) , Holding contact 3 and the close contact 2 of C2.
- When Contactor 1 (C1) is energized, then the two open contact in the line of C1 and C2 will be closed.
- For the specific time (generally 5-10 seconds) in which the motor will be connected in star, after that the Timer contact (Ia) will be open (We may change by rotating the timer knob to adjust the time again) and as a result;
- Contactor 3 (C3) will be off, because of which the open link of C3 will be close (which is in the line of C2) thus C2 will also energize. Similarly, When C3 off, then star connection of winding will also open. And C2 will be closed. Therefore, the motor winding will be connected in Delta. In addition, Contact 2 (which is in the line C3) will open, by which, there would not be any chance of activation of coil 3 (C3)
- Since the motor is connected in Delta now, therefore, each phase of the motor will receive full line voltage (400V) and the motor will start to run in full motion.
- Main Difference between contactor and Starter.
- A simple circuit diagram for understanding the Working of contactor.
- Why We Need to Install a Starter with a Motor?
Power Circuit Diagram of Star Delta Automatic Starter
Click image to enlarge
Control Circuit Diagram of Star Delta Automatic Starter with Timer
Click image to enlarge
Abbreviations: ( FOR Control Wiring of Three Phase Star Delta Starter with Timer)
- R , Y, B = Red, Yellow, Blue ( 3 Phase Lines)
- C.B = General Circuit Breaker
- Main = Main Supply
- Y = Star
- Δ = Delta
- 1a = Timer
- C1, C2, C3 = Contatcors (For Power & Control Diagram)
- O/L = Over Load Relay
- NO = Normally Open
- NC = Normally Closed
- K1 = Contactor (Contactor coil)
- K1/NO = Contactor Holding Coil (Normally Open)
- Starting & Stopping of 3-Phase Motor from more than One Place Power & Control diagrams
- (ON / OFF Three-Phase Motor Connection Power & Control Schematic and Wiring Diagrams)
Advantages of Star Delta Automatic Starter with Timer
- Simple Design and Operation
- Comparatively cheaper than other voltage controlling methods
- Torque and Current performance of the Star delta starter is well.
- It draws two times starting current of the FLA (Full Load Ampere) of the connected motor.
- It reduced the starting current to one-third (approximately) as compared to DOL (Direct ON Line Starter)
- Three Phase Motor Connection Reverse and Forward Power and Control wiring diagrams
- Two Speeds One Direction Three Phase Motor Connection Power and Control Diagrams
- 2 Speeds, 2 Directions Multispeed 3-phase Motor Power & Control Diagrams
Disadvantages of Star Delta Starter with Timer
- Starting Torque is also reduce to one-third because starter reduce the starting current to one-third of the rated current [as Line voltage also reduced to 57% (1/√3)]
- It required Six leads or terminals Motor (Delta Connected)
- For Delta connection, the supply voltage must be same as the rated motor voltage.
- At switching time (From Star to Delta), if the motor does not reach at least 90% of its rated speed, then the current peak may be equally high as in Direct ON Line starter( D.O.L), thus it may cause harmful effects on the contactors contacts, so it would not be reliable.
- We may not use star delta starter if the required (application or load) torque is more than 50% of the three phase induction motors rated torque
You may Also Read Other Power & Control Diagrams here: