## Wire & Cable Size Calculator (Copper & Aluminum)

As we have discussed in detail the topic of “How to calculate the proper wire size for Electrical Wiring. Now you can take the advantage of this calculator to do this job J

- You can also check the classical
**Wire & Cable Size Calculator**in (AWG)

**Calculating Wire/Cable Size formula for single Phase Circuits**

Wire Circular mils =2 x ρ x I x L / (%Allowable Voltage drop of source voltage)

**Calculating Wire/Cable Size formula for Three Phase Circuits**

Wire Circular mils =√3 x 2 x ρ x I x L / (%Allowable Voltage drop of source voltage)

Where;

ρ = Specific resistance or resistivity of Conductor

D = Distance in Feet (One way) i.e. ½ the total circuit length

I = Load Current

Note: the Value of ρ = Specific resistance or resistivity of Conductor is used here for copper and aluminum is 11.2 and 17.4 respectively at 53° C (127° F)

- Also check the “Good to know” Section after the calculator.

Enter value, And click on calculate. Result will show the required quantity.

**Good to Know:**

If the wire size is greater than all gauges (i.e 0000 is largest one size of wire in), then electrical engineer measure it in CM, kCM or MCM instead of inches, because inch is a small unit of these kinds of wires. Where;

A

**circular mil (CM)**is a unit of circular area with a diameter of one mil (one thousandth of an inch). It corresponds to 5.067×10^{-4}mm².Where:

**1000 CM (circular mils)**= 1 MCM or 1 kcmil = 0.5067 mm², so 2 kcmil.

It is a unit for referring to the area of a wire with a circular cross section.

You may also read:

**Enter your Email for Latest Updates like the above one!**

Thanky Thanky for all this good inortmaoifn!

i am balwinder singh ELECTRICIAN controller

above show how to calculate the size of the cable and wire bt it is theoretical right..bt practical not working when i input the data value single phase 230 current 5 A single phase 10 feet voltage drop take 2.5 v ..so please solve my problem

That’s interesting

i need electrical important q&answer

ashfaq.aldawaighri@gmail.com

Hello,

Sir I need cables and wire calculations apps

We are Working on it. Thanks for feedback.

sir

we want to feed 3phase supply to 70 ton air-conditioning load. what will be the size of cable(3 phase) require to feed the 70 ton A.C. load.

what is the copper cable sizing for a 8 kw single phase load 220 volt , 0.8 power factor and 3% voltage drop

8 AWG-CU,6 AWG-AL

Nice information

Sir i have lode 132 kw three phase witch size mm cable proper work

150 sq.mm or 185 sq.mm but length between power source and load should be limited/not very far.

120 sq mm or 150 sq mm. 185 sq mm is not required .

I have 377 Ampere 3-phase connected load to be sourced from 250 KVA 11 KV/440 Volt Distribution Transformer at a distance of 115 metres. What minimum size of 3.5 core Aluminium armoured cable will be suitable for my use.

Sir, I have plan to install 8.3 ton three phase a/c distance between a/c and panel is 45′ voltage drop is 3%. which is the correct size of copper wire i have to use.

Thanks.

10sqmmx4core

10 mm2 * 3 core or 6 mm2

Hello,

I need cables and wire calculations for aluminium and copper, table for diameters and Amp. Thanks.

Hello,

I need cables and wire calculations for aluminium and copper, table for diameters and Amp. Thanks.

Show nice cable matches

how to calculate below

250 meter cable size and 105kw please solve the problem with formula

Hi Everyone,

Kindly give me guidance for the calculation of cable size.

Suppose I have 40A load and 25KA is rating and I don’t have specified lentgh of cable,Voltage ratings but I need to give just size of cable for Phase conductor and ECC is there any way to calculate it directly using some direct formula…?

It is recommended that follow these simple steps then Here and Here. thanks

sir,

what is the distance between high tension electric wire to any building just like ware house, residential building, any factory. thanks

How to calculate mechanical dimensions of Electric cable viz. Aerial bunched cables

Know electrical

What should be the cable size for the following conditions.

1. amps: 3000

2. 3 phase, 440 V

3. Distance : 100 m

3. Laid in trunking, copper cable

Appreciate if you could suggest a cable size?

Thank You

Hello Dear… You can use the online Copper & Aluminum Wire Size calculator with explanation here

nice information

nice information

a generator feeding 420 volt to 380/420 transformer cabble length is 1300 meter.load is of 200 kw.now how to find voltage drop and which cable suits alluminium or copper . and find the diameter of both. please help me out..

Electric cable size wise how much load can be take. I need chart minimum 4 numbers of cable size i.e 1mm, 1.5mm, 2.5mm and 6mm

Example:

Cable 1mm = ?? Amp or, ?? W

Thanks

What should be the cable size for the following conditions.

1. amps: 250

2. 3 phase, 440 V

3. Distance : 100 m

3. Laid in trunking, copper and Aluminumcable

Appreciate if you could suggest a cable size?

Thank You

250 MCM 130mm

250 MCM 130mm2

Sir, I have plan to install 4 no’s of 4 ton three phase a/c distance between a/c and panel is 45′ voltage drop is 3%. which is the correct size of copper wire i have to use.

Thanks.

sir we have 3 kw hot plate it cable is burnout i want to replace it cable high tempatur fiber insulation type length 1mtr only plse helpe me

Dear my supply has 230/380 voltage. But i dont find 380 voltage option in the cable size calculator….?

Hi

How would I determine the size of the main cable to feed 12 houses from a transformer to the main distribution box.

Conditions:

220v

Single phase

45Amp per house x 12

150 Meter (500Feet)

Much appreciated

R

Run is 300 ft. 120/240 volt system 170 amps 3% V.D.

Using wire size 3/0 copper or 250MCM Aluminum.

Is this the correct wire sizing for this project.

Sir

suggest XLPE alluminium Cable for 130A load distance is 500M

Sir.cable & wire(aluminum or copper) how to selection. the load for example..10kw,50kw,125kw,25okw etc. i need to simple formula reply please.