What is a Transformer? Its Parts, Operation, Types, Limitation & Application
What is a Transformer?
- As the name suggest, Transformer transfers electrical power from one electrical circuit to another electrical circuit. It does not change the value of power.
- Transformer doesn’t change the the circuit frequency during operation.
- Transformer works through on electric i.e. mutual induction.
- Transformer operates when both circuits take effect of mutual induction.
- Transformer can’t step-up or step-down the level of DC voltage or DC Current.
- Transformer only step-up or step-down the level of AC voltage or AC Current.
- Transformer doesn’t change the value of flux.
- Transformer won’t operate on DC Voltage.
Without transformers the electrical energy generated at generating stations won’t probably be sufficient enough to power up a city. Just imagine that there are no transformers.How many power plants do you think have to be set up in order to power up a city? It’s not easy to set up a power plant. It is expensive.
Numerous power plant have to be set up in order to have sufficient power. Transformers help by amplifying the Transformer output (stepping up or down the level of voltage or current).
When the number of turns of the secondary coil is greater than that of primary coil, such a transformer is known as step up transformer.
Likewise when the number of turns of coil of primary coil is greater than that of secondary transformer, such a transformer is known as step down transformer.
Construction of a Transformer (Parts of a Transformer)
|1||Oil filter valve||17||Oil drain valve|
|4||Oil filter valve||20||Foundation bolt|
|5||Pressure-relief vent||21||Grounding terminal|
|6||High-voltage bushing||22||Skid base|
|8||Suspension lug||24||Coil pressure plate|
|9||B C T Terminal||25||Core|
|10||Tank||26||Terminal box for protective devices|
|11||De-energized tap changer||27||Rating plate|
|12||Tap changer handle||28||Dial thermometer|
|13||Fastener for core and coil||29||Radiator|
|14||Lifting hook for core and coil||30||Manhole|
|15||End frame||31||Lifting hook|
|16||Coil pressure bolt||32||Dial type oil level gauge|
- Related Post: Open Delta Connections of Transformers
Working Principle of a Transformer
Transformer is a static device (and doesn’t contain on rotating parts, hence no friction losses), which convert electrical power from one circuit to another without changing its frequency. it Step up (or Step down) the level of AC Voltage and Current.
Transformer works on the principle of mutual induction of two coils or Faraday Law’s Of Electromagnetic induction. When current in the primary coil is changed the flux linked to the secondary coil also changes. Consequently an EMF is induced in the secondary coil due to Faraday law’s of electromagnetic induction.
The transformer is based on two principles: first, that an electric current can produce a magnetic field (electromagnetism), and, second that a changing magnetic field within a coil of wire induces a voltage across the ends of the coil (electromagnetic induction). Changing the current in the primary coil changes the magnetic flux that is developed. The changing magnetic flux induces a voltage in the secondary coil.
A simple transformer has a soft iron or silicon steel core and windings placed on it(iron core). Both the core and the windings are insulated from each other. The winding connected to the main supply is called the primary and the winding connected to the load circuit is called the secondary.
Winding (coil) connected to higher voltage is known as high voltage winding while the winding connected to low voltage is known as low voltage winding. In case of a step up transformer, the primary coil (winding) is the low voltage winding, the number of turns of the windings of the secondary is more than that of the primary. Vice versa for step down transformer.
Transformer Always rated in kVA instead of kW.
Transformer Always rated in kVA instead of kW.
As explained earlier, EMF is induced only by variation of the magnitude of the flux.
When the primary winding is connected to ac mains supply, a current flows through it. Since the winding links with the core, current flowing through the winding will produce an alternating flux in the core. EMF is induced in the secondary coil since the alternating flux links the two windings. The frequency of the induced EMF is the same as that of the flux or the supplied voltage.
By so doing (variation of flux) energy is transferred from the primary coil to the secondary coil by means of electromagnetic induction without the change in the frequency of the voltage supplied to the transformer. During the process, a self induced EMF is produced in the primary coil which opposes the applied voltage. The self induced EMF is known as back EMF.
- Related Post: EMF Equation Of a Transformer
Limitation of the Transformer
To understand the main points, we have to discuss some basic terms related to transformer operation. So lets back to basic for a while.
A transformer is an AC machine that steps up or steps down an alternating voltage or current. A transformer being an AC machine however cannot step up or down a DC voltage or DC current. It sounds a bit weird though. You might be thinking “so are there not DC transformers?”
To answer the two questions whether there are or there are not DC transformers and know “why transformer cannot step up or step down a DC voltage” it’s necessary we know how electric current and magnetic field interact with each other in transformer operation.
The interaction between magnetic field and electric current is termed electromagnetism. Current carrying conductors produces magnetic field when current passes through it. Movement of electrons in a conductor will result to electric current (drifted electrons) which occurs as a result of the EMF set up across the conductor.
The EMF set up across the conductor can be in form of that stored in chemical energy or magnetic field. Current carrying conductor placed in a magnetic fields will experience mechanical force while a conductor placed in a magnetic field will have its electrons drifted which will results to electric current.
Two magnets of unlike poles will attract each other while magnets of like poles will repel each other (so it is with electric charges). Every magnet is surrounded by a force field and is represented by imaginary lines emanating from the north pole of a magnet going into the south pole of the same magnet.
Read the important terms related to Field Flux and Magnetic Filed with formulas Here
Electromagnetic induction is a phenomenon that explains how EMF and current is or can be induced in a coil when a coil and a magnetic field interact. This phenomenon”electromagnetic induction”is explained by Faraday’s laws of electromagnetic induction. The direction of induced EMF in a coil is explained by Lenz’s law and Fleming’s right hand rule.
Faraday’s Laws Of Electromagnetic Induction
After Ampere and others investigated the magnetic effect of current, Michael Faraday tried the opposite. In the course of his work he discovered that when there was change in a magnetic field in which a coil was placed, EMF was induced in the coil.
This happened only whenever he moved either the coil or the magnet he used in the experiment. EMF was induced in the coil only when there was change in the field flux (if the coil is fixed, moving the magnet towards or away from the coil causes EMF to be induced). Thus Faraday’s laws of electromagnetic induction states as follows;
Faraday’s First Law
Faraday’s first law of electromagnetic induction states that “EMF is induced in a coil when there is a change in the flux linking the coil”.
Faraday’s Second Law
Faraday’s second law of electromagnetic induction states that “the magnitude of induced EMF in a coil is directly proportional to the rate of change of flux linking the coil”.
e = N dϕ/dt
- e = Induced EMF
- N = the number of turns
- dϕ = Change in flux
- dt = Change in time
Lenz’s law entails how the direction of an induced EMF in a coil can be determined. “It thus states that the direction of induced EMF is such that it opposes the change causing it.
In other words, When an E.M.F is induced in a circuit, the current setup always opposes the motion, or change in current, which produces it. OR
An induced EMF will cause a current to flow in a close circuit in such a direction what its magnetic effect will oppose the change that produced it.
According to this law (which introduced by Lens in 1835), the direction of current can be found. when the current through a coil changes magnetic field, the voltage is created as a result of changing magnetic field, the direction of the induced voltage is such that it always opposes the change in current.
Fleming’s Right Hand Rule
It states that “if the thumb, the forefinger and the middle finger are held in such a way that they are mutually perpendicular to each other (makes 90° of Angles), then the forefinger points the direction of the field, the thumb points the direction of motion of the conductor and the middle finger points the direction of the induced Current (from EMF).
Why Transformers Can’t step Up Or Step Down A DC Voltage or Current?
A transformer cannot step up or step down a DC voltage. It is not recommendable to connect a DC supply to a transformer because if a DC rated voltage is applied to the coil (primary) of a transformer, the flux produced in the transformer will not change in its magnitude but rather remain the same and as a result EMF will not be induced in the secondary coil except at the moment of switching on, So the transformer may start to smock and burn because;
In case of DC supply, Frequency is zero. When you apply voltage across a pure inductive circuit, then according to
XL= 2 π f L
- XL = Inductive Reactance
- L = Inductance
- f = Frequency
if we put frequency = 0, then the overall XL (inductive reactance) would be zero as well.
Now come to the current, I = V / R (and in case of inductive circuit, I = V / XL) …. basic Ohm’s Law
If we put Inductive reactance as 0, then the current would be infinite (Short circuit)…
So, If we apply DC voltage to a pure inductive circuit, The circuit may start to smoke and burn.
Thus transformers are not capable of stepping up or stepping down a DC voltage. Also there will be no self induced EMF in such cases in the primary coil which is only possible with a varying flux linkage to oppose the applied voltage. The resistance of the primary coil is low and as such a heavy current flowing through it will result to the primary coil burning out due to excessive heat produced by the current.
Types of Transformers
There are different types of transformer based on their usage, design, construction as follow.
Types of Transformers based on its Phases
- Single Phase Transformer
- Three Phase Transformer
Types of Transformers based on its Core Design
- Core Type Transformer
- Shell Type Transformer
- Berry Type Transformer
Types of Transformers based on its Core
- Air core Transformer
- Ferromagnetic/Iron Core Transformer
Types of Transformer based on its usege
- Large Power Transformer
- Distribution Transformer
- Small Power Transformer
- Sign Lighting Transformer
- Control & Signalling Transformer
- Gaseous Discharge Lamp Transformer
- Bell Ringing Transformer
- Instrument Transformer
- Constant Current Transformer
- Series Transformer for Street Lighting
Related Post: Difference between Power and Distribution Transformers?
Types of Transformer based on Insulation & Cooling
- Self Air Cooled or Dry Type Transformer
- Air Blast-Cooled Dry Type
- Oil Immersed, Self Cooled (OISC) or ONAN (Oil natural, Air natural)
- Oil Immersed, Combination of Self Cooled and Air blast (ONAN)
- Oil Immersed, Water Cooled (OW)
- Oil Immersed, Forced Oil Cooled
- Oil Immersed, Combination of Self Cooled and Water Cooled (ONAN+OW)
- Oil Forced, Air forced Cooled (OFAC)
- Forced Oil, Water Cooled (FOWC)
- Forced Oil, Self Cooled (OFAN)
Types of Instrument Transformer
- Current Transformer
- Potential Transformer
- Constant Current Transformer
- Rotating Core Transformer or Induction regulator
Related Post: Power Transformer Protection & Faults
Uses and Application of Transformer
Uses and applications of transformer is discussed already in this previous post.
Advantages of 3-Phase Transformer over 1-Phase Transformer
Read the advantages and disadvantages of Single Phase & three phase transformer here.
- Transformer Performance & Electrical Parameters
- Transformers Insulation Materials in Oil-Immersed & Dry Type T/F
- Transformers Fire Protection System – Causes, Types & Requirements
- Advantages and Disadvantages of Three Phase Transformer over Single Phase Transformer.
- Transformer Phasing: The Dot Notation and Dot Convention
- Can We Replace a 110/220 Turns Transformer with 10/20 Turns?
- Electrical Transformer Symbols – Single Line Transformer Symbols
- Can We Operate a 60Hz Transformer on 50Hz Supply Source and Vice Versa?