How to Find The Suitable Size of Cable & Wire for Electrical Wiring Installation? – Examples in Imperial & Metric System
How to Determine the Proper Size of Wire & Cable for Electrical Wiring Installation?
The following step by step guide will show you how to find the right size of cable and wire or any other conductor for electrical wiring installation with solved examples (in both British or English and SI System i.e. Imperial and Metric System respectively).
Keep in mind that it is very important to select proper wire size while sizing a wire for electrical installations. An inappropriate size of wire for bigger loads having high current may create chaos which leads to failure of the electrical equipment, hazardous fire and serious injuries.
Table of Contents
Voltage Drop in Cables
We know that all conductors, wires and cables (except superconductors) have some amount of resistance.
This resistance is directly proportional to the length and inversely proportional to the diameter of conductor i.e.
R ∝ L/a … [Laws of resistance R = ρ (L/a)]
Whenever current flows through a conductor, a voltage drop occurs in that conductor. Generally, voltage drop may be neglected for small length of conductors but in case of a lower diameter and long length conductors, we have to take into account the considerable voltage drops for proper wiring installation and future load management.
According to IEEE rule B23, at any point between power supply terminal and installation, Voltage drop should not increase above 2.5% of the provided (supply) voltage.
Related Posts:
 How to Find the Proper Size of Circuit Breaker? Breaker Calculator & Examples
 How to Find the Voltage & Ampere Rating of Switch, Plug, Outlet & Receptacle
 How to calculate the Cable size for LT & HT Motors?
Example:
If the supply voltage is 220V AC, then the value of allowable voltage drop should be;
 Allowable Voltage Drop = 220 x (2.5/100) = 5.5V
Similarly, if the supply voltage is 120V AC, the allowable voltage drop should be no more than 3V ( 120V x 2.5%).
In electrical wiring circuits, voltage drops also occur from the distribution board to the different sub circuit and final sub circuits, but for sub circuits and final sub circuits, the value of voltage drop should be half of that allowable voltage drops (i.e. 2.75V of 5.5V as calculated above)
Normally, Voltage drop in tables is described in Ampere per meter (A/m) e.g. what would be the voltage drop in a one meter cable which caries one Ampere current?
There are two methods to define the voltage drop in a cable which we will discus below.
In SI (System international and metric system) voltage drop is described by ampere per meter (A/m).
In FPS (foot pound system) voltage drop is described in length based which is 100 feet.
 Update: Now you may also use the following electrical Calculators to find Voltage drop & the wire size in American wire gauge systems.
 Electrical Wire & Cable Size Calculator (Copper & Aluminum)
 Wire & Cable Size Calculator in AWG
 Voltage Drop in Wire & Cable Calculator
Tables & Charts for Proper Cable & Wire Sizes
Below are the important tables which you should follow for determining the proper size of cable for Electrical Wiring Installation.
Click image to enlarge
Click image to enlarge
Click image to enlarge
Click image to enlarge
Click image to enlarge
How to Find the Voltage Drop in a Cable?
To find voltage drop in a cable, follow the simple steps given below.
 First of all, find the maximum allowable voltage drop.
 Now, find the load current.
 Now, according to the load current, select a proper cable (which current rating should be nearest to the calculated load current) from table 1.
 From Table 1, find the voltage drop in meter or 100 feet (what system you prefer) according its rated current.
(Stay cool :) We will follow both methods and systems for finding voltage drops (in meters and 100 feet) in our solved example for whole electrical installation wiring).
 Now, calculate the voltage drop for the actual length of the wiring circuit according to its rated current with the help of following formulas.
(Actual length of circuit x volt drop for 1m) /100 ===> to find Volt drop in per meter.
(Actual length of circuit x volt drop for 100ft) /100 ===> to find volt drop in 100 feet.
 Now multiply this calculated value of volt drop by load factor where;
Load factor = Load Current to be taken by Cable/ Rated Current of Cable given in the table.
 This is the value of Volt drop in the cables when load current flows through it.
 If the calculated value of voltage drop is less than the value calculated in step (1) (Maximum allowable voltage drop), than the size of selected cable is proper
 If the calculated value of voltage drop is greater than the value calculated in step (1) (Maximum allowable voltage drop), than calculate voltage drop for the next (greater in size) cable and so on until the calculated value of voltage drop became less than the maximum allowable voltage drop calculated in step (1).
Related Posts:
 How to Find the Size of Earth Conductor, Earthing Lead & Earth Electrodes?
 How to Do Electrical Earthing? – Methods and Types of Earthing & Grounding (Step by Step)
 How to Control One Lamp From Two or Three Places?
How to Determine the Proper Cable & Wire Size for Given Load?
Below are solved examples showing how to find the proper Cable Size for Given Load.
For a given load, cable size may be found with the help of different tables but we should keep in mind and follow the rules about voltage drop.
Determining the size of cable for a given load, take into account the following rules.
For a given load except the known value of current, there should be 20% extra scope of current for additional, future or emergency needs.
From Energy meter to Distribution board, Voltage drop should be 1.25% and for final sub circuit, voltage drop should not exceed 2.5% of Supply voltage.
Consider the change in temperature, when needed, use temperature factor (Table 3)
Also, consider the load factor when finding the size of cable
When determining the cable size, consider the wiring system i.e. in an open wiring system, temperature would be low but in conduit wiring, temperature increases due to the absence of air.
 Note: Keep in mind Diversity Factor in Electrical Wring Installation while selecting the proper size of cable for electrical wiring installation
Related Posts:
 How to calculate the value of resistor for LEDs (with different types of LED’s circuits)
 How To Locate Faults In Cables? Cable Faults, Types & Causes
 Why Coaxial Cables are Highly Insulated?
Solved Examples of Proper Wire & Cable Size
Following are the examples of determining the proper Size of cables for electrical wiring installation which will make it easy to understand the method of “how to determine the proper size of cable for a given load”.
Example 1 … (Imperial, British or English System)
For Electrical wiring installation in a building, Total load is 4.5kW and total length of cable from energy meter to sub circuit distribution board is 35 feet. Supply voltages are 220V and temperature is 40°C (104°F). Find the most suitable size of cable from energy meter to sub circuit if wiring is installed in conduits.
Solution:
 Total Load = 4.5kW = 4.5 x1000W = 4500W
 20% additional load = 4500 x (20/100) = 900W
 Total Load = 4500W + 900W = 5400W
 Total Current = I = P/V = 5400W /220V =24.5A
Now select the size of cable for load current of 24.5A (from Table 1) which is 7/0.036 (28 Amperes). It means we can use 7/0.036 cable according to table 1.
Now check the selected (7/0.036) cable with temperature factor in Table 3, so the temperature factor is 0.94 (in table 3) at 40°C (104°F) and current carrying capacity of (7/0.036) is 28A, therefore, current carrying capacity of this cable at 40°C (104°F) would be;
Current rating for 40°C (104°F) = 28 x 0.94 = 26.32 Amp.
Since the calculated value (26.32 Amp) at 40°C (104°F) is less than that of current carrying capacity of (7/0.036) cable which is 28A, therefore this size of cable (7/0.036) is also suitable with respect to temperature.
Now find the voltage drop for 100 feet for this (7/0.036) cable from Table 4 which is 7V, But in our case, the length of cable is 35 feet. Therefore, the voltage drop for 35 feet cable would be;
Actual Voltage drop for 35 feet = (7 x 35/100) x (24.5/28) = 2.1V
And Allowable voltage drop = (2.5 x 220)/100 = 5.5V
Here The Actual Voltage Drop (2.1V) is less than that of maximum allowable voltage drop of 5.5V. Therefore, the appropriate and most suitable cable size is (7/0.036) for that given load for Electrical Wiring Installation.
Example 2 … (SI / Metric / Decimal System)
What type and size of cable suits for given situation
 Load = 5.8kW
 Volts = 230V AV
 Length of Circuit = 35 meter
 Temperature = 35°C (95°F)
Solution:
Load = 5.8kW = 5800W
Voltage = 230V
Current = I = P/V = 5800 / 230 = 25.2A
20% additional load current = (20/100) x 5.2A = 5A
Total Load Current = 25.2A + 5A = 30.2A
Now select the size of cable for load current of 30.2A (from Table 1) which is 7/1.04 (31 Amperes). It means we can use 7/0.036 cable according to the table 1.
Now check the selected (7/1.04) cable with temperature factor in Table 3, so the temperature factor is 0.97 (in table 3) at 35°C (95°F) and current carrying capacity of (7/1.04) is 31A, therefore, current carrying capacity of this cable at 40°C (104°F) would be;
Current rating for 35°C (95°F) = 31 x 0.97 = 30 Amp.
Since the calculated value (30 Amp) at 35°C (95°F) is less than that of current carrying capacity of (7/1.04) cable which is 31A, therefore this size of cable (7/1.04) is also suitable with respect to temperature.
Now find the voltage drop for per ampere meter for this (7/1.04) cable from (Table 5) which is 7mV, But in our case, the length of cable is 35 meter. Therefore, the voltage drop for 35 meter cable would be:
Actual Voltage drop for 35meter =
= mV x I x L
= (7/1000) x 30×35 = 7.6V
And Allowable voltage drop = (2.5 x 230)/100 = 5.75V
Here the actual Voltage drop (7.35V) is greater than that of maximum allowable voltage drop of 5.75V. Therefore, this is not a suitable size of cable for that given load. So we will select the next size of selected cable (7/1.04) which is 7/1.35 and find the voltage drop again.
According to Table (5) the current rating of 7/1.35 is 40 Amperes and the voltage drop in per ampere meter is 4.1 mV (See table (5)). Therefore, the actual voltage drop for 35 meter cable would be;
Actual Voltage drop for 35 meter =
= mV x I x L
(4.1/1000) x 40×35 = 7.35V = 5.74V
This drop is less than that of maximum allowable voltage drop. So this is the most appropriate and suitable cable or wire size.
Related Posts:
 How to Connect a Portable Generator to the Home Supply – 4 Methods
 How to Connect Automatic UPS / Inverter to the Home Supply System?
Example 3
Following Loads are connected in a building:
SubCircuit 1
 2 lamps each o 1000W and
 4 fans each of 80W
 2 TV each of 120W
SubCircuit 2
 6 Lamps each of 80W and
 5 sockets each of 100W
 4 lamps each of 800W
If supply voltages are 230 V AC, then calculate circuit current and Cable size for each SubCircuit?
Solution:
Total load of SubCircuit 1
= (2 x 1000) + (4 x 80) + (2×120)
= 2000W + 320W + 240W = 2560W
Current for SubCircuit 1 = I = P/V = 2560/230 = 11.1A
Total load of SubCircuit 2
= (6 x 80) + (5 x 100) + (4 x 800)
= 480W + 500W + 3200W= 4180W
Current for SubCircuit 2 = I = P/V = 4180/230 = 18.1A
Therefore, Cable suggested for sub circuit 1 = 3/.029” (13 Amp) or 1/1.38 mm (13 Amp)
Cable suggested for SubCircuit 2 = 7/.029” (21 Amp) or 7/0.85 mm (24 Amp)
Total Current drawn by both SubCircuits = 11.1A + 18.1A = 29.27 A
So cable suggested for MainCircuit = 7/.044″ (34 Amp) or 7/1.04 mm (31 Amp)
Related Posts:
 American Wire Gauge “AWG” Chart – Wire Size & Ampacity Table
 American Wire Gauge (AWG) Calculator – AWG Size Chart & Table
 Standard Wire Gauge “SWG” Calculator – SWG Size Chart & Table
Example 4
A 10H.P (7.46kW) three phase squirrel cage induction motor of continuous rating using StarDelta starting is connected through 400V supply by three single core PVC cables run in conduit from 250feet (76.2m) away from multiway distribution fuse board. Its full load current is 19A. Average summer temperature in Electrical installation wiring is 35°C (95°F). Calculate the size of the cable for the motor?
Solution:
 Motor load = 10H.P = 10 x 746 = 7460W *(1H.P = 746W)
 Supply Voltage = 400V (3Phase)
 Length of cable = 250feet (76.2m)
 Motor full load Current = 19A
 Temperature factor for 35°C (95°F) = 0.97 (From Table 3)
Now select the size of cable for full load motor current of 19A (from Table 4) which is 7/0.36” (23 Amperes) *(Remember that this is a 3phase system i.e. 3core cable) and the voltage drop is 5.3V for 100 Feet. It means we can use 7/0.036 cable according Table (4).
Now check the selected (7/0.036) cable with temperature factor in table (3), so the temperature factor is 0.97 (in table 3) at 35°C (95°F) and current carrying capacity of (7/0.036”) is 23 Amperes, therefore, current carrying capacity of this cable at 40°C (104°F) would be:
Current rating for 40°C (104°F) = 23 x 0.97 = 22.31 Amp.
Since the calculated value (22.31 Amp) at 35°C (95°F) is less than that of current carrying capacity of (7/0.036) cable which is 23A, therefore this size of cable (7/0.036) is also suitable with respect to temperature.
Load factor = 19/23 = 0.826
Now find the voltage drop for 100feet for this (7/0.036) cable from table (4) which is 5.3V, But in our case, the length of cable is 250 feet. Therefore, the voltage drop for 250 feet cable would be;
Actual Voltage drop for 250feet = (5.3 x 250/100) x 0.826 = 10.94V
And maximum Allowable voltage drop = (2.5/100) x 400V= 10V
Here the actual Voltage drop (10.94V) is greater than that of maximum allowable voltage drop of 10V. Therefore, this is a not a suitable size of cable for the given load. So we will select the next size of selected cable (7/0.036) which is 7/0.044 and find the voltage drop again. According to Table (4) the current rating of 7/0.044 is 28 Amperes and the volt drop in per 100 feet is 4.1V (see Table 4). Therefore, the actual voltage drop for 250 feet cable would be;
Actual Voltage drop for 250 feet =
= Volt drop per 100 feet x length of cable x load factor
= (4.1/100) x 250 x 0.826 = 8.46V
And Maximum Allowable voltage drop = (2.5/100) x 400V= 10V
The actual voltage drop is less than that of maximum allowable voltage drop. So this is the most appropriate and suitable cable size for electrical wiring installation in a given situation.
NEC Wire Size Table 310.15(B)(16) (formerly Table 310.16) & Chart
NEC (National Electrical Code) Table 310.15(B)(16) (formerly Table 310.16) – 310.60 – ARTICLE 310 – Conductors for General Wiring & Allowable Ampacities of Conductors & Wire Sizes based on AWG (American Wire Gauge).
310.60 ARTICLE 310 — CONDUCTORS FOR GENERAL WIRING  
Table 310.15(B)(16) (formerly Table 310.16) Allowable Ampacities of Insulated Conductors Rated Up to and Including 2000 Volts, 60°C Through 90°C (140°F Through 194°F), Not More Than Three CurrentCarrying Conductors in Raceway, Cable, or Earth (Directly Buried), Based on Ambient Temperature of 30°C (86°F)*  
Size AWG or kcmil  Temperature Rating of Conductor [See Table 310.104(A).]  Size AWG or kcmil  
60°C (140°F)  75°C (167°F)  90°C (194°F)  60°C (140°F)  75°C (167°F)  90°C (194°F)  
Types TW, UF  Types RHW, THHW, THW, THWN, XHHW, USE, ZW  Types TBS, SA, SIS, FEP, FEPB, MI, RHH, RHW2, THHN, THHW,
THW2, THWN2, USE2, XHH, XHHW, XHHW2, ZW2 
Types TW, UF  Types RHW, THHW, THW, THWN, XHHW, USE  Types TBS, SA, SIS, THHN, THHW,
THW2, THWN2, RHH, RHW2, USE2, XHH, XHHW, XHHW2, ZW2 

COPPER  ALUMINUM OR COPPERCLAD ALUMINUM  
18**  —  —  14  —  —  —  — 
16**  —  —  18  —  —  —  — 
14**  15  20  25  —  —  —  — 
12**  20  25  30  15  20  25  12** 
10**  30  35  40  25  30  35  10** 
8  40  50  55  35  40  45  8 
6  55  65  75  40  50  55  6 
4  70  85  95  55  65  75  4 
3  85  100  115  65  75  85  3 
2  95  115  130  75  90  100  2 
1  110  130  145  85  100  115  1 
1/0  125  150  170  100  120  135  1/0 
2/0  145  175  195  115  135  150  2/0 
3/0  165  200  225  130  155  175  3/0 
4/0  195  230  260  150  180  205  4/0 
250  215  255  290  170  205  230  250 
300  240  285  320  195  230  260  300 
350  260  310  350  210  250  280  350 
400  280  335  380  225  270  305  400 
500  320  380  430  260  310  350  500 
600  350  420  475  285  340  385  600 
700  385  460  520  315  375  425  700 
750  400  475  535  320  385  435  750 
800  410  490  555  330  395  445  800 
900  435  520  585  355  425  480  900 
1000  455  545  615  375  445  500  1000 
1250  495  590  665  405  485  545  1250 
1500  525  625  705  435  520  585  1500 
1750  545  650  735  455  545  615  1750 
2000  555  665  750  470  560  630  2000 

Here is the NEC table as a chart (image format to downloads as a reference)
Click image to enlarge
 How to Size a Load Center, Panelboards and Distribution Board?
 How to Determine the Number of Circuit Breakers in a Panel Board?
 How to Determine the Right Size Capacity of a Subpanel?
 How to Calculate the Suitable Capacitor Size in Farads & kVAR for Power factor Improvement
 How to Convert Capacitor Farads into kVAR & Vice Versa (For Power factor improvement)
 How To check a Capacitor with Digital & Analog Multimeter. 8 Methods
 How to Check the Value of Burnt Resistor. 3 Handy methods
 How To: Electrical & Electronics Tutorials
 Basic Electrical Wiring Installation Tutorials
Thanks Sir,<br /><br />It Gives me all the answers for my question.<br /><br />Thanks Once Again.
Welcome Dear….and Thanks 4 appreciation…
For 10kv how much sqmm ug cable can put
Thank you so much. Please don’t stop your work. Great.
Ya I need assistance
Sir
can you help me how to Know the cable size and suitable MCCB rating(example i have 120sqmm x4 core aluminium and 100MCCB is suitable for the above size cable if is not suitable what are possible problem may occureed)
Sir I could not get this "Number of wires & Thikness of each wires" (7 / 0.0229)……….. (70 / 0.0076)<br />Kindly give me answer.<br />
Dear @<br /> 7/0.029 means 7 numbers of wires ( Conductors in a cable) and diameter of each conductor is 0.029" inches.
I think it is: 7 wire strands, each with a 0.029 inch diameter, in a single conductor cable. Is this correct?
Dear sir.,<br />great valuable explanation . i am realy searching this stuff from past 3 years. not i got it just sake of ur study material.
Seems like I am doing exam's numerical, but thanks so much for this post. With high quality cable if you do not know how much the length should it be, then the resistance will be more. And these tables for calculating the Voltage drop really helped a lot
Thanks for Appreciation
Located in Tianchang city, Anhui province, Tianchang Zhengjie Wire Drawing Die Factory is a professional manufacturer of diamond wire drawing dies in China. <a href="http://www.philatron.com/wirecablemanufacturer/" rel="nofollow">SBR cable</a><br />
sir, can you tell me how to fish a wire through a conduit pipe..
I have a 130 watts panel charging a 120ah battery,and 500 watts inverter.I have connected 65watts TV,decoder,4 15watts lights and 100watts laptop.Looking at the load am I doing the right thing.
<a href="www.https://www.electricaltechnology.org/2013/05/acompletenoteonsolarpanel.html" rel="nofollow"> A Complete note on Solar panel Installation </a>
Great Work Boss.
Thanks for appreciation
Dear sir,
On above discussion, selection of cable size you are considered voltage drop should not be less than (+ or – 2.5%) of our supply voltage, But according to electricity distributor allowable voltage fluctuation is (+ or – 5%).
please clear my that confusion.
Thanks in advance
Sir,, Plz also explain in new assignments <br />1.how we calculate Breaker Size and its nature? as MCB, MCCB, ACB, VCB <br />2. Calculation of BusBar size w.r.t load ?<br />Thanx
Thanks for Positive feedback,,, Wait for the upcoming posts..
Thank you v much for this useful information…….. Stay blessed.
Welcome Dear, and bundle of thanks for best wishes..
Great Job,thanks a lot for the post.
Thanks for Appreciation
the cable the tech's glove is on has pulled down so much that it is in contact in two places; the upper right meter contact, and the cable guide to the right. <a href="http://500mcmcable.com/" rel="nofollow">750 mcm cable</a><br />
make a thread where show how to do home conduit wiring n all<br />btw grt work
This blog is very informative and I would like to see some more blogs on this topic.<br /><a href="http://www.kowelec.com.au/aboutus/" rel="nofollow">Experienced Industrial Electricians At Kowelec Bendigo</a>
gud job you gave the information about copper cables only..wat abt Alluminium armoured cables<br />
than you so much for this useful link
Great site. Wondering the source of tables, is it from any standards? ie. IEC, NEC, etc.<br />Thanks.
sir plz mention the standard according to which the tables have been made.<br /><br />
i want selection of flexible cable standard chart with electric load
If you look carefully at the calculations there are some basic mistake which would effect the final result. ie 2 TV's @ 150w ea. is the shown as 2 x 120w. Other mistake include the lenght calculated which starts at 250 feet then goes to 35 feet and then back to 250 feet.
These are just Examples…. You have to find the suitable size of cable for wiring according to your specification and load requirements… Any way thanks for correction.
sir plz mention the standard according to which the tables have been made.
Thanks for Positive and important Questions.<br />lets try to answer<br /><br />(1)<br />In clear words (for your first Question)<br /><br />Temperature factor means that when temperature increases, Cable/Wire or conductor resistance also increase, hence, Cable/Wire or conductor current carrying capacity decreases. For instance; <br />If the current carrying capacity of wire or cable is 28 Ampere
I am not an electrical engineer, but why does a higher temp in table 3 result in lower temp factor (which makes the calculated value less than the current carrying capacity)? For instance in example 1 – take 43 amps in the table times a temp factor of .94 to yield 40.42 amps. The results is always less than initial amps unless you use a lower temp. Therefore, the higher the temp, the lower the
Would you tell me about the IEC standard in Electrical Installation design and the importance of IEC standard. <br />Thanks for your nice post
if increase frequency value r decrease then what will happen?
Dear Sir.
Thank u very much much for deep explanation.
Do we need to consider power factor in the calculation of load current…..
But,when temprature of conductor increases then resistivty decreases.
When temperature increase resistivity increase too
Dear Sir,
I want to know that if we have no table and we do not remember the current caring capacity of conductor than how can we calculate the cable size? We know the total load, Temperature, Area from DB to load. Please guide.
Good day sir,
Great explanation, but the only aspect am confused of is the area of cable determination,i was expecting the sizes of cable in mm sq as against 7/0.036
thanks for the simple and straight forward language for communication. Please how did you arrive at 5800KW in example 2 above.
Thanks for Appreciation… But where is 5800kW in Example 2… It is 5.8kW = 5800W. :)
thankz a lot bro
nice it’s very helpful for me thanks
I have to install 2 hp single phase pump set load carrying 13 to 15 amps. voltage at site is 220 to 230 volts. Length of cable will be 500 mtrs. Can you suggest required cable size in Copper as well as alluminium ?
Reply me on my email
dear sir
i want to find cable size in mm for the load of 600 amp and the main breaker is 1000 amp area is 120 meters supply voltage is 380 v three phase .
Did You check this?
https://www.electricaltechnology.org/2014/12/advancevoltagedropcalculatorvoltagedropformula.html
i have a motor 3phases 227 kw i want to connect it to the soft starter which size of cable i have to use ?
also can i use 3cores instead of one core so the connection it will be inplace of 3cx…. 9 cores
each pahse will atke three cores Q!?
May Allah ( God ) Bless you for your this type of kind effort , it’s very helpful for me and for electrical related engineers
thanks
how to calculate 3 phase 400 v and 600 amp load’s cable size which must have a length of 25 meter
You can find it by using this calculator. You may also use this one.
how we can make selection of cable for our system
Dear sir, You have done a great job. It’s very helpful to me. You may live long.
Amarasiri from SL.
Thanks for your kind words… :)
dear sir,
please tell me relation between your cabe size(total coductor/ Diameter of each) and square mm cable size
eg. 7/085 cable= ……sq.mm
Dear any body feed back regarding cable selection depending load & length of cable 3 phase application
used cable size is 10 mm load 34.6 Amps 460 .3Ph 60 hz motor
Hi,
What size cable do I need to run 325metres from an 80amp transformer on the power pole so I still have 63amps at the end?
Thank you very much for your assistance.
Sorry, forgot to mention it needs to be 3phase
Are all made computations, in the samples above, AC or DC? Pleas I need answer.
I have responsibility to provide 150kVA genset to one of social concernt where they have 75kVA sound system with 20 nos of 250W Floodlightings. But my duty is to provide them above generator and power cable reaching to their Main DB panel.
Now, advice me which power cable should I go with the suitable size please???
Please, what size of cable can I use to wire an equipment of 3phase, 4wire 120KVA, 50Hz with power factor of 0.8?
This 7core configuration doesnt fit with NEC standards I think. We use 4c or 3c as per requirement. I am seeing for the first time like 7C..?
What formula is followed to make the table? I want to know in given load, length of cable which electrical calculation can be done to find out the size of cable?
Current rating for 40°C (104°F) = 28 x 0.94 = 26.32 Amp.
Since the calculated value (26.32 Amp) at 40°C (104°F) is less than that of current carrying capacity of (7/0.036) cable which is 28A, therefore this size of cable (7/0.036) is also suitable with respect to temperature.
I think this para is trying to say that if temperature increases the current carrying capacity or rating would decrease for the same size of cable. So it means that if my load current is less than the calculated rating of the wire then we can use the wire. So it should say “Since the calculated value (26.32 Amp) at 40°C (104°F) is less than that of load current which is 24.5A, therefore this size of cable (7/0.036) is also suitable with respect to temperature.”
This is with reference to example 1. Please correct if i am wrong.
state two factors to be considered in selection of cables sizes for a house wiring
sir, I have a farm for which I want to put 10 numbers of 25 watts CFL bulbs around the perimeter, the perimeter of the farm is around 1 KM. Can you please confirm what type of wire I need to use (gauge, insulation requirements, Copper vs Aluminum), Considering that I will be laying this underground through pipes (which might be exposed to water at times…I need wires that are resistant to moisture and soil interaction). I am planning on using drip pipes which are cheaper and pass the wires through them. Please advise. This will be run on solar power. I will size the solar power unit accordingly.
I want to know about it.
If you have a time or see this comment, Please reply me.
In example 1,
Why are you using that I = P/V?
Total Current = I = P/V = 5400W /220V =24.5A
Actually, It should be which is I = P/( V x PF)
Assume , Power Factor (PF) will be 0.8.
Total Current = I = P/( V x PF) = 5400W /( 220 x 0.8)V =30.68 A
bro I= P/V for DC and I= P/V x PF for AC Power
What is power factor?
You may read about
sir plz mention the standard according to which the tables have been made.
Total load 32 KW 3phase 4wire system (distribute)220 volt 1phase and length 140 Meter .what is cable size use in mm
sir, please provide below information with necessary calculations
for 200/150 HP/Kw 3phase induction motor
1. cable size from pannel to starter to motor and from HT transformer to LT pannel
2. type of starter to be used
3. Type of pannel to be used
thanks
Can you please tell me which Electrical Code did you use in above calculations?
I have 3phase 10 HP Moto ,16 amps,which size cable is sutiable,iam Diploma EEE,Fresher on maintenance Engineer on on eharama company,plz give me cable size flexible or armed cable.core and mm size plzz give,mee
you are calculating full load current of a 3 phase motor. that doesnot include sq.root of 3.
I Thank You Mr. Khan, for your great effort in helping your visitors with an easy to understand presentation. I must tell you you are the best online teacher and you understood what basics people must know before they would understand the subject matter. I guess you must be a generous human being who is helping others not to fail in life. keep up the effort!
Thanks again!
Thank you so much for appreciation,,,, :)
Honestly i enjoyed the tutorials, its quite interesting for all engineering student both graduates and under graduates… i appreciate the effort of electrical technology for her convenient idea of letting some techs into us. Thanks alot
Many thanks, for your outstanding efforts in educating and assisting all peoples to understand such valuable technical subjects.
Good explaination of calculating the size of the cable.
I got this (V.D of m = mV x I x L) a bit confusing. How is this formula derived? If you apply the values and their units, ypu dont get volts per ampere meter at the end.
Can you justify please.
Thanks for the information about electrical wiring
how to find out 240RM cable , which is actual system
great work
how did you find load factor for the last example ? we have replace the selected cable with new one, why do you choose the same load factor ?
Which questions are asking for industrial electrician in interview please reply
thank you very much, it is very useful, I hope you give us more examples of threephase circuits.
Best regards.
Eng. Abdolgabar Ahmed Mahmood.
Great article about wiring and installation.
Short and brief description thank you.
I want to ask about question number 4
In load factor, at first calculation of cable size(load factor)=19/23=0.82
But, after we change the cable size with higher size, why the load factor use in calculation still 0.82, isn’t that (load factor)=19/28?
Previously, i want to say thank you, this website is very incredible
First, i thank. In eg.1 the load factor is 24.5/ 28. In eg.2 it is change into I and is not 30.2/31 . Why is it. Please reply me if you have time. Pardon me if i wrote faulty because i am not fluency in english. Thank.
sir, my Q is how find / calculate the amps if the conductor size of cable is 32/0.2 mm and v 440
Dear sir
Please answer this
20 HP,415 v,0.8 of,3phase,0.85efficiency,1440 rpm and delta connected induction motor is to be connected to a motor control center by a cable of length 15 m,this cable is running with three other cables,ambient temperature is 45 degree Celsius and fault level is 20 KA,select the size of the cable from below
PVC cable 300mm.value of k/cu 103.value of k/al 68
XLPE cable <300mm.value of k/cu 114.value of k/al 92
It’s really great job to learn online from basic to till all experience fields i would like to have a request for lesson
1. Testing & commission of electrical equipment in substaion
2. CNC machines , types , work principles
3. Site Engineer work in Substaions
4. Single line diagram module and it’s implementation
5. QA or QC work and their Electrical Standards.
It will be very thankful if you can provide these important lessons to us to gain knowledge through your website atleast with video upload to have knowledge in theory as well as in practicle
Hello ….. could you please calculate the 3phase question using the metric table. The answer I am getting is unrealistic.
Hi Thomas ?
Can you please elaborate more in details ?
Sir,
I requesting to you please, make the blog and video of electrical wiring installation of any flate/home.
And your blogs are so useful for us.
Thanking you.
Having determine my total load requirements after considering all factors
for example say load current is 750A for a 3phase supply
If l want to use single core pvc/ pvc cable
Do l divide the 750A by 3 before chosen the corresponding cable size from the catalog or not
Regards
Bosun
Good way of describing, and nice piece of writing to obtain data about my presentation subject, which i am going
to convey in school.
Tanks you sir
How to connecting RCCB and RCB
Hi!
I use more simple way. I find R of cable R=ρ ×L/A, where
R is the resistance of the conductor in Ohms;
L is the length of the conductor in meters;
ρ is the electrical resistivity (also known as the specific electrical resistance) of a conductor, for cooper ρ=0,018 Ohm · mm²/m;
A is the crosssectional area, measured in square millimeters.
Then find voltage drop
for L+N voltage system, dU (V)= I×R×2,
for L+L voltage system, dU (V)= I×R,
Where I is a current in wire;
dU(V) is a voltage drop in volt.
And in the end I find dU in %
dU(%)=dU(V)×100/U
where U is a line voltage.
Sorry for my english.
Very good sir.
Thank you for this blog
Please add tutorials about MC, CB, O/L, FUSE, T/F, generators and motors suitable size calculations.
Hi, I am very impress of this blog . It is very much helpful for us as electrical engineer students in our respective areas of interest .
Please , for the information above , I really want a PDF copy of it .
Thanks once more …
Assalam alikum sir
Why power factor is not taken in calculation as it is AC circuit?
I am very impressed of ur blogs. pl post a table of cable & alu conductor current rating of different sizes to b use in ht/ lt lines in state utilities in day today practice.