**How to determine the suitable size of cable for Electrical Wiring Installation**

**Voltage drop in Cables**

**Example:**if the Supply voltage is 220V, then the value of allowable voltage drop should be;

**voltage drop in a cable**which we will follow.

In FPS (foot pound system) voltage drop is described in 100feet.

**Update**: Now you can also use the following Calculators to find Voltage drop & the wire size in American wire gauge.

**Tables & Charts for Suitable Cable & Wire Sizes**

### **To find voltage drop in a cable, follow these simple steps**

- First of all, find the maximum allowable voltage drop
- Now, Find load current
- Now, according to load current, select a proper cable (which current rating should be nearest to the calculated load current) from table 1
- From Table 1, find the voltage drop in meter or 100feet (what system you prefer) according its rated current

(Stay cool 🙂 we will follow both methods and system for finding voltage drops (in meter and 100feet) in our solved example for whole electrical installation wiring).

- Now, calculate the voltage drop for the actual length of wiring circuit according to its rated current with the help of
.**following formulas**

(Actual length of circuit x volt drop for 1m) /100 —-> to find Volt drop in per meter.

(Actual length of circuit x volt drop for 100ft) /100—> to find volt drop in 100feet.

- Now multiply this calculated value of volt drop by load factor where;

Load factor = Load Current to be taken by Cable/ Rated Current of Cable given in the table.

- This is the value of Volt drop in the cables when load current flow through it.
- If the calculated value of voltage drop is less than the value calculated in step (1) (Maximum allowable voltage drop), than the size of selected cable is proper
- If the calculated value of voltage drop is greater than the value calculated in step (1) (Maximum allowable voltage drop), than calculate voltage drop for the next (greater in size) cable and so on until the calculated value of voltage drop became less than the maximum allowable voltage drop calculated in step (1)

**How to determine the proper Cable Size for Given Load (with Examples)**

- Note: Keep in mind Diversity Factor in Electrical Wring Installation while selecting the proper size of cable for electrical wiring installation

**Solved Examples of Proper Wire & Cable Size**

**Example 1 ………..**

*(British / English System)***Solution:-**

- Total Load = 4.5kW = 4.5 x1000W = 4500W
- 20% additional load = 4500 x (20/100) = 900W
- Total Load = 4500W + 900W = 5400W
- Total Current = I = P/V = 5400W /220V =24.5A

**Current rating for 40°C (104°F) = 28 x 0.94 = 26.32 Amp.**

**Example 2 ……. ( SI / Metric / Decimal System )**

**Solution:-**

**Total Load Current = 25.2A + 5A = 30.2A**

**table 1**.

**Current rating for 35°C (95°F) = 31 x 0.97 = 30 Amp.**

**= mV x I x L****most appropriate and suitable cable or wire size**.

**Example 3**

*Sub-Circuit 1*

- 2 lamps each o 1000W and
- 4 fans each of 80W
- 2 TV each of 120W

*Sub-Circuit 2*

- 6 Lamps each of 80W and
- 5 sockets each of 100W
- 4 lamps each of 800W

**Solution:-**

**Total load of Sub-Circuit 1**

**Total load of Sub-Circuit 2**

*= 3/.029” (13Amp) or 1/1.38mm (13Amp)*

**Cable suggested for sub circuit 1****= 7/.029” (21Amp) or 7/0.85mm (24Amp)**

*Cable suggested for Sub-Circuit 2***= 7/.044” (34Amp) 0r 7/1.04mm (31Amp)**

*cable suggested for Main-Circuit***Example 4**

**Solution:-**

**Motor load**= 10H.P = 10 x 746 = 7460W *(1H.P = 746W)**Supply Voltage**= 400V (3-Phase)**Length of cable**= 250feet (76.2m)**Motor full load Current**= 19A**Temperature factor**for 35°C (95°F) = 0.97 (From Table 3)

**Current rating for 40°C (104°F) = 23 x 0.97 = 22.31 Amp.****Load factor = 19/23 = 0.826**

**How to Calculate the Suitable Capacitor Size in Farads & kVAR for Power factor Improvement (Easiest way ever)****How to Convert Capacitor Farads into kVAR & Vice Versa (For Power factor improvement)****How To check a Capacitor with Digital & Analog Multimeter. 4 Methos****How to Check the Value of Burnt Resistor. 3 Handy methods****How To: Electrical & Electronics Tutorials**

**Enter your Email for Latest Updates like the above one!**

**From Schematic to PCB Production, Just Need One Tool - EasyEDA**

Free Circuit Design Software: learn to use Editor quickly and easily

Cheapest PCB: 10pcs 2-layers 10cm×10cm only $8.21, 3-day build time, 100% E-test

Thanks Sir,<br /><br />It Gives me all the answers for my question.<br /><br />Thanks Once Again.

Welcome Dear….and Thanks 4 appreciation…

Thank you so much. Please don’t stop your work. Great.

Sir I could not get this "Number of wires & Thikness of each wires" (7 / 0.0229)……….. (70 / 0.0076)<br />Kindly give me answer.<br />

Dear @<br /> 7/0.029 means 7 numbers of wires ( Conductors in a cable) and diameter of each conductor is 0.029" inches.

I think it is: 7 wire strands, each with a 0.029 inch diameter, in a single conductor cable. Is this correct?

Dear sir.,<br />great valuable explanation . i am realy searching this stuff from past 3 years. not i got it just sake of ur study material.

Seems like I am doing exam's numerical, but thanks so much for this post. With high quality cable if you do not know how much the length should it be, then the resistance will be more. And these tables for calculating the Voltage drop really helped a lot

Thanks for Appreciation

Located in Tianchang city, Anhui province, Tianchang Zhengjie Wire Drawing Die Factory is a professional manufacturer of diamond wire drawing dies in China. <a href="http://www.philatron.com/wire-cable-manufacturer/" rel="nofollow">SBR cable</a><br />

sir, can you tell me how to fish a wire through a conduit pipe..

I have a 130 watts panel charging a 120ah battery,and 500 watts inverter.I have connected 65watts TV,decoder,4 15watts lights and 100watts laptop.Looking at the load am I doing the right thing.

<a href="www.electricaltechnology.org/2013/05/a-complete-note-on-solar-panel.html" rel="nofollow"> A Complete note on Solar panel Installation </a>

Great Work Boss.

Thanks for appreciation

Dear sir,

On above discussion, selection of cable size you are considered voltage drop should not be less than (+ or – 2.5%) of our supply voltage, But according to electricity distributor allowable voltage fluctuation is (+ or – 5%).

please clear my that confusion.

Thanks in advance

Sir,, Plz also explain in new assignments <br />1.how we calculate Breaker Size and its nature? as MCB, MCCB, ACB, VCB <br />2. Calculation of BusBar size w.r.t load ?<br />Thanx

Thanks for Positive feedback,,, Wait for the upcoming posts..

Thank you v much for this useful information…….. Stay blessed.

Welcome Dear, and bundle of thanks for best wishes..

Great Job,thanks a lot for the post.

Thanks for Appreciation

the cable the tech's glove is on has pulled down so much that it is in contact in two places; the upper right meter contact, and the cable guide to the right. <a href="http://500mcmcable.com/" rel="nofollow">750 mcm cable</a><br />

make a thread where show how to do home conduit wiring n all<br />btw grt work

This blog is very informative and I would like to see some more blogs on this topic.<br /><a href="http://www.kowelec.com.au/about-us/" rel="nofollow">Experienced Industrial Electricians At Kowelec Bendigo</a>

gud job you gave the information about copper cables only..wat abt Alluminium armoured cables<br />

than you so much for this useful link

Great site. Wondering the source of tables, is it from any standards? ie. IEC, NEC, etc.<br />Thanks.

sir plz mention the standard according to which the tables have been made.<br /><br />

i want selection of flexible cable standard chart with electric load

If you look carefully at the calculations there are some basic mistake which would effect the final result. ie 2 TV's @ 150w ea. is the shown as 2 x 120w. Other mistake include the lenght calculated which starts at 250 feet then goes to 35 feet and then back to 250 feet.

These are just Examples…. You have to find the suitable size of cable for wiring according to your specification and load requirements… Any way thanks for correction.

sir plz mention the standard according to which the tables have been made.

I am not an electrical engineer, but why does a higher temp in table 3 result in lower temp factor (which makes the calculated value less than the current carrying capacity)? For instance in example 1 – take 43 amps in the table times a temp factor of .94 to yield 40.42 amps. The results is always less than initial amps unless you use a lower temp. Therefore, the higher the temp, the lower the

Thanks for Positive and important Questions.<br />lets try to answer<br /><br />(1)<br />In clear words (for your first Question)<br /><br />Temperature factor means that when temperature increases, Cable/Wire or conductor resistance also increase, hence, Cable/Wire or conductor current carrying capacity decreases. For instance; <br />If the current carrying capacity of wire or cable is 28 Ampere

Would you tell me about the IEC standard in Electrical Installation design and the importance of IEC standard. <br />Thanks for your nice post

if increase frequency value r decrease then what will happen?

Dear Sir.

Thank u very much much for deep explanation.

Do we need to consider power factor in the calculation of load current…..

But,when temprature of conductor increases then resistivty decreases.

Dear Sir,

I want to know that if we have no table and we do not remember the current caring capacity of conductor than how can we calculate the cable size? We know the total load, Temperature, Area from DB to load. Please guide.

Good day sir,

Great explanation, but the only aspect am confused of is the area of cable determination,i was expecting the sizes of cable in mm sq as against 7/0.036

thanks for the simple and straight forward language for communication. Please how did you arrive at 5800KW in example 2 above.

Thanks for Appreciation… But where is 5800kW in Example 2… It is 5.8kW = 5800W. 🙂

thankz a lot bro

nice it’s very helpful for me thanks

I have to install 2 hp single phase pump set load carrying 13 to 15 amps. voltage at site is 220 to 230 volts. Length of cable will be 500 mtrs. Can you suggest required cable size in Copper as well as alluminium ?

Reply me on my email

dear sir

i want to find cable size in mm for the load of 600 amp and the main breaker is 1000 amp area is 120 meters supply voltage is 380 v three phase .

Did You check this?

http://www.electricaltechnology.org/2014/12/advance-voltage-drop-calculator-voltage-drop-formula.html

i have a motor 3phases- 227 kw i want to connect it to the soft starter which size of cable i have to use ?

also can i use 3cores instead of one core so the connection it will be inplace of 3cx…. 9 cores

each pahse will atke three cores Q!?

May Allah ( God ) Bless you for your this type of kind effort , it’s very helpful for me and for electrical related engineers

thanks

how to calculate 3 phase 400 v and 600 amp load’s cable size which must have a length of 25 meter

You can find it by using this calculator. You may also use this one.

how we can make selection of cable for our system

Dear sir, You have done a great job. It’s very helpful to me. You may live long.

Amarasiri from SL.

Thanks for your kind words… 🙂

dear sir,

please tell me relation between your cabe size(total coductor/ Diameter of each) and square mm cable size

eg. 7/085 cable= ……sq.mm

Dear any body feed back regarding cable selection depending load & length of cable 3 phase application

used cable size is 10 mm load 34.6 Amps 460 .3Ph 60 hz motor

Hi,

What size cable do I need to run 325metres from an 80amp transformer on the power pole so I still have 63amps at the end?

Thank you very much for your assistance.

Sorry, forgot to mention it needs to be 3-phase

Are all made computations, in the samples above, AC or DC? Pleas I need answer.

I have responsibility to provide 150kVA genset to one of social concernt where they have 75kVA sound system with 20 nos of 250W Floodlightings. But my duty is to provide them above generator and power cable reaching to their Main DB panel.

Now, advice me which power cable should I go with the suitable size please???

Please, what size of cable can I use to wire an equipment of 3-phase, 4-wire 120KVA, 50Hz with power factor of 0.8?

This 7core configuration doesnt fit with NEC standards I think. We use 4c or 3c as per requirement. I am seeing for the first time like 7C..?

What formula is followed to make the table? I want to know in given load, length of cable which electrical calculation can be done to find out the size of cable?

Current rating for 40°C (104°F) = 28 x 0.94 = 26.32 Amp.

Since the calculated value (26.32 Amp) at 40°C (104°F) is less than that of current carrying capacity of (7/0.036) cable which is 28A, therefore this size of cable (7/0.036) is also suitable with respect to temperature.

I think this para is trying to say that if temperature increases the current carrying capacity or rating would decrease for the same size of cable. So it means that if my load current is less than the calculated rating of the wire then we can use the wire. So it should say “Since the calculated value (26.32 Amp) at 40°C (104°F) is less than that of load current which is 24.5A, therefore this size of cable (7/0.036) is also suitable with respect to temperature.”

This is with reference to example 1. Please correct if i am wrong.

state two factors to be considered in selection of cables sizes for a house wiring

sir, I have a farm for which I want to put 10 numbers of 25 watts CFL bulbs around the perimeter, the perimeter of the farm is around 1 KM. Can you please confirm what type of wire I need to use (gauge, insulation requirements, Copper vs Aluminum), Considering that I will be laying this underground through pipes (which might be exposed to water at times…I need wires that are resistant to moisture and soil interaction). I am planning on using drip pipes which are cheaper and pass the wires through them. Please advise. This will be run on solar power. I will size the solar power unit accordingly.

I want to know about it.

If you have a time or see this comment, Please reply me.

In example 1,

Why are you using that I = P/V?

Total Current = I = P/V = 5400W /220V =24.5A

Actually, It should be which is I = P/( V x PF)

Assume , Power Factor (PF) will be 0.8.

Total Current = I = P/( V x PF) = 5400W /( 220 x 0.8)V =30.68 A

sir plz mention the standard according to which the tables have been made.

Total load 32 KW 3phase 4wire system (distribute)220 volt 1phase and length 140 Meter .what is cable size use in mm

sir, please provide below information with necessary calculations

for 200/150 HP/Kw 3-phase induction motor

1. cable size from pannel to starter to motor and from HT transformer to LT pannel

2. type of starter to be used

3. Type of pannel to be used

thanks

Can you please tell me which Electrical Code did you use in above calculations?

I have 3phase 10 HP Moto ,16 amps,which size cable is sutiable,iam Diploma EEE,Fresher on maintenance Engineer on on eharama company,plz give me cable size flexible or armed cable.core and mm size plzz give,mee

you are calculating full load current of a 3 phase motor. that doesnot include sq.root of 3.

I Thank You Mr. Khan, for your great effort in helping your visitors with an easy to understand presentation. I must tell you you are the best online teacher and you understood what basics people must know before they would understand the subject matter. I guess you must be a generous human being who is helping others not to fail in life. keep up the effort!

Thanks again!

Thank you so much for appreciation,,,, 🙂